He very nice and did a good job
We were impressed with Shane. Very personable and knowledgeable
On time and very efficient
Very professional and courteous
Other than a small miscommunication on time everything was fine.
I enjoyed Jamie, he really knew what he was doing and was very polite. Have me his opinion on what I should do
Experienced technician and great service.
Steve has been servicing our HVAC equipment since we bought the home 4 years ago. He knows his job, and gives us good tips to keep it maintained and running well.
Found condensate overflow switcj shutting power off to thermostat. Blew condensate line out amd added treatment. Verified system operation.
Found compressor shorted to ground. Sent info. in to shop to give quote or possible warranty.
Found the electric heater was on in cool mode, found and repaired a short on the stat cable, checked operations.
Found and replaced the burn 3 amps AHU fuse, found and replaced the shorted condenser contactor, checked operations.
Performed first start on system. Removed nitrogen pulled system into A vacuum of 500 microns. Released refrichecked system operations in cooling and heating all ok. System operating and draining correctly at this time.
Tripped breaker,reset. System operating &functioning properly
Looked at inside of flex and boot in each bathroom and verified there was no mold. Only had dust on inside from dust sticking to moisture from bathroom.
Installed new thermostat provided by owner and set up to run existing equipment. Hooked up electric strip heat that had never been wired up. Restored power and verified proper operation.
Customer getting own financing,will call back and ask for 473 only
Left phone message &tagged door
Found sequencer melted, replaced sequencer & replaced burnt wires & ordered fan board again board shorted
Left est for T-stat, customer going to replace
Performed the annual check up, all modes work promptly at this time.
Fan board shorted, was not listed, sent to parts for quote, add $67 to quote