Bay Area Air conditioning is a top their company and every employee that we have dealt with has provided exceptional service. Mr. Milligan was here on an annual service call, performed the service and left detailed notes on the system and performance. He also fixed a problem with the UV light and the electrostatic filter that I was unaware of. Thanks.
As usual, Bay Area does a great job! Highly recommend them. The service man was courteous and did a wonderful job.
Got here right at 8 AM, did his work and on his way.
We had Dave check Freon which was up to specs. Dave also leak tested the A- coils and compressor and was not able to find any leaks. When the unit was installed the refrigerant lines were not replace since they run under the concrete floor through a conduit. We assume the lines are original and my be corroded and almost impossible to remove to install new lines but no one has attempted the task. We plan to have your company move the compressor off our patio and new lines installed at that time. However, we must gain approval and permits from On Top of the World Management. If they approve the move and issue a permit, we will contact you to complete the job.
Every step of the way was efficient and professional. Very pleased and would refer to anyone with confidence.
Have been a customer since 2012 and heartily recommend Bay Area! Thanks, Glenn!
Found the system off on code 77 and 95. Checked the grounds and the compressor windings. I've reset the system and everything came back on and js cooling down for now. I would recommend replacing the inverter. Putting in a parts order and reschedule to return with the part. Installed the inverter and got the system up and cooling. Note: code 99 on system number 2. Need to order a part and schedule to return. Returned and replaced the condenser fan motor on system 2 the two ton.
Found the system off on code 77 and 95. Checked the grounds and the compressor windings. I've reset the system and everything came back on and js cooling down for now. I would recommend replacing the inverter. Putting in a parts order and reschedule to return with the part.
1st year warranty System shutting off on float switch safety. Cleaned and flushed drain line. Restarted and tested cooling and drain line.
Customer stated stopped cooling in the middle of the night. Float switch did not trip, unit continued to run. Checked capacitor, refrigerant charge, split temps. Customer said heard sound when occurred and had storm. System straight cool and suspect power drop cause compressor off on ol from run backwards momentarily.
Replaced shorted dual run capacitor. Restarted cooling 10 parts and labor.
Compressor wire burnt and disconnected. Repair wire and test. System operating at this time. Recommend replacing system. Recall, customer states CC on file. New equipment quote left at last call.
Located and repaired 230 volt connection to contactor. Replaced weak run capacitor Charge to credit card on file
repaired leak on liquid line by filter drier. Leak tested and evacuated system. Rplaced lost 410a. Restarted and tested sub cooling. Warranty
Found no issue with the air conditioning system itself the problem is with the generac system, remove the wiring from the air handler breaker and connected the air handler wiring to the air handler breaker to allow cooling until the customer get generac out to fix the problem
Spoke with Mrs. on phone, she was able to provide specific details letting me conclude the slight intermittant popping/gurgling noise is coming from the drain vent pipe. The noise is not evident when their ac is on indicating some other ac either a floor above or below is not trapped and is pulling air thru the common riser in the wall back thru the vent pipe. Mrs. will have Mr. call me with any questions
Upon arrival the blower motor would not ramp up to speed. I quoted evergreen module. They accepted quote and I installed new module, it is cooling at this time.
Found error codes 41 and 44. Found a bad blower motor. Also the system is in poor condition and should be replaced.
Found the noise coming from the reversing valve. After working on the unit for about ten minutes the noise went away. Could be an intermittent noise from the reversing valve. I also noticed a refrigerate leak at the condenser coil. The air handler is from 2016 but the condenser's serial number is faded off and appears to by older as all of its screws and bolts.are rusting.
System maintenance on heatpump system. Replaced air filter. 2 of 2 systems. Collecting for both on this invoice.