Unit operating, filter impacted. Removed filter which made a marginal improvement but TD is still very low. Check refrigerant and amp draw, conclusion is system is doing what it can, but not able to maintain temperature in peak temperatures of summer. 21 yrs old and R22. Recommend replacing system with new Carrier AC system. Quote new equipment.