Closed service valves and tried to pull the refrigerant into the condenser. Valves would not fully seat. Refrigerant was going back to the coil. Used reclaimer and reclaimed refrigerant into tank. Cut linset and removed wiring. Capped wires and disconnected disconnect. Moved condenser into garage per customer. Once concrete is done, customer will have condenser reset. Refrigerant will need to be added at that time. Job complete.