No heat. Cycled system. Blower and ventor motor run but no ignition. Checked high limit, ok. Checked and jumpers rollout switch, system fired. Reset rollout switch, system cycled. Office will follow up after checking with the warranty company about possible part replacement. System operating normal at this time. Recommend full cleaning of system.