Technician was super nice
Hunter did a good job explaining what he did and what we needed to do with settings. Very personable young man.
Everything went great and Julian was nice and easy to work with, he explained things well to us.
Great experience, very nice work on the install, high quality product
Highly recommended! Very pleased with two service trips to date. Impressed with how thorough and professional the technicians and supervisor that also came by today were.
Performed furnace clean and tune; inspected the exhaust and intake PVC ensuring all connections were secured, removed and cleaned the burners along with the flame sensor, cycled the system on and checked gas pressures, as well as performed a combustion test verifying no CO in the airstream. I did leave a 213 aprilaire filter behind. This system is currently operating normal and heating at 62 degrees at this time. Job complete
Furnace safety inspection. Cycled system. Checked heat exchanger. Found both chambers very rusted and worn. Found deep etching in both. Igniter worn and flame sensor is worn. Found exhaust venting not glued in two places. One near the termination, the other from the ventor motor. Both venting pipes were glued and checked, ok, Found the ventor motor very worn. Bearings are bad in motor. Checked levels of CO and XS air in exhaust. CO is normal, but XS air is high. 170. Found large area of rust in blower compartment. Cleared drain lines. Rust damage may be due to location in basement and leaking water issues from foundation. No CO found in airstream. System is 16 years old. Average life of this unit is 14 years. System is very worn and has issues, but operating safety at this time. Future failure is expected, but passes current inspection guidelines. Job complete.
Performed the level 2 boiler cleaning. Burners and flame sensor were inspecte. Heat exchanger looks good. Exhaust and CO levels are normal. Water pressure and temperatures were good. Unit is heating properly at this time.
Performed preferred customer furnace cleaning. Cleaned the burners and the flame sensor. Checked the furnace heat exchanger. Wiped down the inside of the furnace. Cycled the furnace. Checked the motors for proper operation. Performed furnace combustion test. Checked for carbon monoxide in the air stream. Found water inside the inducer motor. Cleaned the furnace drain trap and drain line. Found a dirty furnace filter. Replaced the furnace filter. The furnace is running normally at this time. Looks like the air conditioner hasnâ€™t been checked in a while. Recommended getting an air conditioning cleaning to make sure the air conditioner is running properly and efficiently.
Came out to investigate a no heat. I found the inducer would kick in and the gas valve would click, but the igniter wouldnâ€™t get hot. The igniter was bad so I replaced it. System is operating normally at this time.
Was here for a furnace no heat. Found that the inducer motor bearings are seizing up and not allowing the inducer motor to start. Changed out the inducer motor. Cycled the furnace. The furnace is running normally at this time.
Cut old pvc exhaust pipe apart at the wall near where it exits the basement. Re-piped the exhaust from outside in to where the horizontal run begins at main beam. Installed three new 3â€ pvc 90â€™s and one new 3â€ 45. Cleaned and glued fittings taking care to make sure they didnâ€™t push apart. Using an s-slip I shimmed the plenum above humidifier to cause the upper portion of the humidifier body to lean back slightly. This in turn leveled the front of the humidifier housing. Ran the humidifier for several minutes to check for any leaks and found the water to only be running into drain as it should. Thank you for choosing Black-Haak Heating. Please take a moment to fill out our online survey.
Performed furnace clean and tune; inspected the exhaust and intake PVC ensuring all connections were secured, I then removed and cleaned the burners along with the flame sensor as well as performed heat exchanger powder test and did get blowback from all 3 cells, cycled the system on and checked gas pressures, as well as performed a combustion test verifying no CO in the airstream. This system is currently operating normal at this time. Job complete
Unwired and removed old pressure switch. Wired and installed new pressure switch. Cleared pressure tubes. Cycled system, heating normal at this time. Job complete.
Replacement of Blower Motor I removed the failed blower motor from the geo unit. I mounted the new blower motor in the unit. I wired up the blower motor. Cycled the unit. Itâ€™s operating properly at this time. Geo has a 20 degree temperature rise which is good.
The customer has a package cleaning. Was here for the furnace portion of the cleaning. Performed preferred customer furnace cleaning. Completed furnace cleaning form. The furnace is running normally at this time. Office to call to schedule the appointment in the spring for the air conditioner cleaning.
Installed 14x25x1 electronic Air cleaner. Job complete
Was here for a furnace cleaning. Performed preferred customer furnace cleaning. Completed furnace cleaning form. The furnace is running normally at this time.
Performed first year furnace cleaning; system was not getting up to temp upon arrival found a clogged 201 air filter the system was going out on high limit due to the clogged filter, I replaced the the 201 filter for the mean time no charge because we upgrading to the electronic air cleaner, I then removed and cleaned the burners along with the flame sensor, I then cycled the system on and checked gas pressures, then performed a combustion test verifying no CO in the airstream. This system is currently operating normal and heating at 48 degrees at this time. We will have to return to install the air cleaner. Job complete
Completed gas furnace replacement. Disconnected the old furnace and removed it from the basement. Set new furnace on blocks and then reconnected the electric, gas, pvc venting and ductwork. Installed a new T6 programmable thermostat and connected it to the furnace. Reconnected the furnace and humidifier drains. Run tested the furnace but will still need a technician start up. Thank you for choosing Black-Haak Heating. Please take a moment to fill out our online survey.