Very happy to see Jorge after two days of no air
This survey is for our 2nd appointment with Jorge.
They quickly diagnosed the problem and ordered the needed part immediately.
Jorge was polite and professional and they gave me prompt service with a smile.
Always honest fair service
Although the serviceman was young, he was very impressive with knowledge of his field and with his people skills I felt respected as a person and valued as a customer
Courteous and knowledgable men. Michaela the receptionist worked us in and was much appreciated.
Commercial clean VAV coils and change filters
See hvac call attachment
Completed one system fall inspection on Goodman furnace. Unit is operating properly at this time and heating the house well. No problems detected. Also co.pleted plumbing inspection as well. No leaking water anywhere. All fixtures could be upgraded but as far as functionality plumbing is operating just fine.
Unit was running intermediately turning on and off. After diagnostic drain lines were clogged again. I tore apart the drainlines, cleaned the insides of the pvc and cleared the clog. Unit is running at this time.
Called to downstairs not cooling well on Saturday (ambient temp 104) after inspection of units downstairs capacitor was failing on fan side. I replaced the capacitor and unit is cooling at time of departure
Estimate to replace all rooftop units with split systems OR RTU systems.
Completed one system diagnostic. Upon first diagnosis I thought system was just a couple of lbs low on refrigerat. But when filling the system the TXV started not regulating the refrigerant properly. Recommended replacement of the TXV. Customer paid for the 2lbs of refrigerat and signed up for a monthly club membership.
Drain line pipe had crack in it and was leaking all over floor. Replaced 90 degree pipe and water stopped leaking.
System running upon arrival. Charged system with two pounds of 410-a refrigerant. System cooling at this time.
No cool replaced a burn contactor on a Trane system