Came out to perform preventative maintenance for air conditioning system. Also to find out why system was leaking water all over the basement floor. Upon inspection I found the filter to be fully clogged and the drains had a chunk of debris at the outlet of the pan. Removing debris and changing the filter fixed the issue. Inspected all the electrical components. Confirmed proper high and low voltages. Tested the temperature split between the supply and return. System was operating at a 20° differential on an 81° day. Tested the amp draw for the blower, compressor and fan motor. All were operating within the manufacturer specs. Tested the condensate pump. Pump is operating properly at this time and drain is clear. System is operating properly at this time.