Had A/C maintenance done as part of the Planned Maintenance Agreement. The technician found that the dual capacitor was in bad shape so I had that replaced, and it was partly covered by the Carrier warranty. There's a lot to be said for preventive maintenance, especially when it is done by a reliable company. I've been a Classic Aire Care customer for 7 years now.
What I appreciate best about Classic Air Care is the customer service and clear communications. From the office staff to the technicians, we have never been disappointed and also learn a great deal about our HVAC maintainance.
Classic Aire Care is fortunate to have Roger Henson represent their company in service visits. A most impressive man who competently installed our new lo-ambient kit. He also leaned-in willingly to lead the trouble-shooting of an additional situation and brought it to a simple and effective resolution. In addition, he was responsive to and able to clarify all of our questions. We are grateful for his help in establishing a new Planned Maintenance Agreement as well. Roger Henson is unmatched in our service visit experiences....standing out in any evaluation criteria utilized. Please send Roger for all our PMA service visits!
John arrived promptly, checked everything insid and out. My air conditioner got a clean bill of health. Love these guys at Classic Aire.
This is the first time I have worked with Classic Aire and I was very satisifed with the service and knowledge of my technician.
Had a service Interruption on one of the holidays and service response was within 3 to 4 hours.
Second floor system: I found system very low on Freon. Found evaporator coil oily and leaking Freon. Needs new evaporator coil. I charged up system for temporary cooling. Expect Freon to last a week or two. Work suggested: system uses old type of Freon. Recommend replacing air conditioner for second floor system. John C. to call customer.
Main system: I found dual capacitor bad. Open circuit. I replace dual capacitor under parts only warranty. Compressor overload reset. Tested operation.
I found bad start assist kit, bad compressor run capacitor (dual), weak fan capacitor: 25% low. Also, condenser coil is very dirty. I replaced defective parts. Tested cooling operation and found system approximately 20 to 30% low on Freon! uses (R22)! Suction: 72 (43) suction line: 78. Metering device: TXV. Head pressure: 208. Subcooling: 0 to 2. Thermostat: 89. Customer plans to have a friend add Freon. Work suggested: recommend putting some repair costs toward replacement. Need to schedule project manager to price out new air conditioner. customer purchased maintenance plan today. Need to schedule first visit.
Turned on system. Was set at 70. Found high temperature drop. 23. Found 3M pleated air filter restricting flow, causing System to ice up. Replaced air filter. Blew out clogged drain trap. Checked system for leaks. Found evaporator coil leaking. Needs new evaporator coil. Work suggested: recommend fiberglass type air filters. Air filters to be delivered. Need to check on cost and availability replacement of evaporator coil for air handler.
Comfortmaker air conditioner replaced dual run capacitor
I found dual run capacitor bad. Open circuit. I replaced dual capacitor. Tested cooling operation.
Nordyne air conditioner replaced condenser fan motor and capacitor
I found corrosion on thermostat battery terminal. Cleaned off corrosion and tested thermostat. Cut out restrictive ribbon. Tested AC operation. Found low on Freon. (Superheat at target +11) I topped off (R22) Freon level. Leak search declined at this time. First floor: recommend thermostat batteries.
Lennox air conditioner replaced condenser fan motor and fan blade
I found blower motor bearings dragging. Motor won’t start. Also found weak run capacitor. 35% low. I replaced blower capacitor and oiled bearings for temporary cooling. Work suggested: furnace is 33 years old. Recommend replacing. John C. To price new furnace today.
I replace blower motor and wheel. And tested operation. Blower: 6.7A. liquid line: 99 . suction line: 47. metering device piston . Return air: 76.5 . supply air: 55.5 . wet bulb: 62 .
Lennox air conditioner replaced dual run capacitor
I reclaimed Freon from system. I removed and replaced compressor. Replaced bi-flow liquid line filter/drier. Cleaned and checked air conditioner per schedule PSCC. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Cleaned condenser coil. Charged system. Compressor: 15.9A. Condenser fan: 1.1A . Blower: 1400 . ambient: . liquid line: 103 . suction line: 61 . metering device: TXV . Suction pressure:149(53) . head pressure: 361(109).
Serviced air conditioner and replaced capacitor
Maintenance on air conditioner with Ameren rebate