I found blower motor having trouble starting. Found run capacitor very weak: 46% low, causing low starting torque. Also, Blower motor bearings have play. Worn. Customer declined this repair. Also, the furnace in need of cleaning. Cleaned & checked gas furnace per new maintenance plan. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Checked filter. Replaced weak capacitor. Set speed and test. Blower: 4.0A . Inducer: 0.89A . Temperature rise: 56 . Supply: 124 . Return: 68 .