This was the first time John came to do the maintenance on my furnace. He was very knowledgeable and professional. I have used metal tape to seal up a lot of duct work, he pointed out other areas to seal that no other technician had shown me.
We've been using Classic Aire Care for a couple of years. We signed up for their maintenance program where they show up every quarter to look over our equipment, change filters, clean blowers and compressors, and make sure the system is working up to standards. They are quick to point out potential issues and give an estimate to how much life might be left in a questionalble component. They've never been wrong and our heating and AC have always performed flawlessly, winter and summer! Can't say enought good things about these find folks.
I depend on you to take care of ny heating and cooling needs.
Service was professional and fast. Service was on time and the worker was able to answer all my questions.
Roger is a great technician. He has many years of experience. He is always friendly and personable. and very efficient in getting the job done. it was great that he had Brian with him, and providing more on the job training for Brian's career and future
the technician was very professional and did great work
Roger always does a great job at servicing my furnace. He explained in detail some upcoming repair work that I will have done also. Scott was here also servicing my plumbing. he also explained in detail the replacement of my water heater, and modifications to be made to fit the new one in the space. he and Roger worked together on the scope of the job to be done as it will involve some modifications needed to my heating ducts too. it was great that they were both here at the same time to discuss the job.
Checked heat pump system. Replaced air filter. found system low on Freon! Performed Freon leak search. Discovered indoor coil leaking bad on left side near the bottom. I picked up a new coil at Lennox. Pumped down system. Removed and replaced coil using nitrogen purge and brazing alloy. Evacuated lower side. Recharged in cooling mode. Compressor: 4.4A. Condenser fan: 0.77A . ambient: 62. liquid line: 68 suction line: 38-45 . CC: 72. metering device: TXV . Suction pressure: 106(34). head pressure: 208(72). Return air: 67 . supply air: 42 . wet bulb: 50.
Customer explained that moaning noise that lasts about two seconds occurs periodically, about 20 seconds after burners light but before blower comes on. Noise would not appear! Replaced air cleaner media. I secured furnace bottom. Adjust blower speeds. Calibrated humidy reading. We heard a very faint noise once, several seconds before blower came on while standing by thermostat.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Checked filter. Gas pressure: 1.8 inches water column. Temperature rise: 44. Supply: 119. Return: 75 . Clean and check humidifier, replace pad, checked water flow and drain.
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Test capacitor. Replaced air filter. tested thermostat batteries. Blower: 1.7/2.3A . Inducer: 0.54/1.5A . Gas pressure: 1.8/3.5 inches water column. Temperature rise: 51/66 . Supply: 145 . Return: 79 .
Cleaned & checked gas furnace. Inspected heat exchanger & flue venting. cleaned burners & flame sensor. Checked voltage & amp draw of motors. Blower: 1.8A . Inducer:0.53A . Replaced air filter.
Cleaned and checked air conditioner. Checked drain. Checked voltage and amperage draw of motors. Tested capacitors. Checked Freon level. Replaced air filter. I found compressor not re-starting! Has reciprocating compressor with a non-equalizing metering device! I installed a start assist kit to ensure compressor starts every time. Has very thick condenser coil and very dirty. Back-flushed condenser coil with Water-Saber.
Serviced ac and replaced filter
Maintenance for AC system!
Replaced evaporater coil
Topped off Freon till new system is installed
Spring maintenance for both AC systems!
Found evaporater coil leaking,replacing coil
Serviced ac and replaced customer supplied filters
Spring maintenance on AC system! Good to go
Replaced compressor and evaporator coil. NO CHARGE. Warranty. Homeowner signed up for maintenance plan!