Found condensate pump float safety tripped. Pump not able to pump water through frozen line that goes to the outside. Humidifier was installed last year and connected to this existing condensate pump system. Condensate pump system works for warm weather only. No charges today. Suggestions: run new condensate discharge line over to drain stack where washing machine drains.