Very professional and fast
Found main level system low on 410a, recharged and added in leak sealers. Found basement system low on 410a, recharged system. Signed customer up for 2 system maintenance plan and went ahead and did summer maintenance. Changed upstairs filter, basement filter is clean. Mechanical and electrical components in good shape. Added chlorine tablets to evap coil drain pans. Chemically washed condenser coils and added rust proof waxing. Systems operating at this time.
No cool upstair system. Check and find fault in voltage absorption system. Renovate voltage absorption HN4C with performance enhancement upgrade, install relay and repair wire with new connections, add 1/2 lbs of charge for proper cooling and meet manufacture spec. System operating at this time. Suggest plan to help maintain system and prolong system life.
Found furnace power switch off. Turned it on and system is operating. Went ahead and checked electrical components for customer. Found blower motor controller running weak out of manufacturer specs, recommend repair. Found water safety not up to code, recommend adding on. Found very rusty evap coil. Found system low on r22, recommend recharging. Found serious pitting on voltage distribution system, recommend repair. Found slight burning on common wire/ terminal going into the voltage absorption system and a weak voltage absorption system. Recommend repair. Installed new blower motor controller. Added on water safety so it is now up to code. Recharged system to 10 degrees superheat. Replaced voltage distribution system. Replaced voltage absorption system and Renovated electrical terminations. Signed customer up for maintanence plan and went ahead and did summer maintenance. Left customer with a replacement filter. Cleared drain line. Chemically washed condenser coil and applied rust pro
1 system ac tune up complete. Changed filter. Found rusty evap coil. Found no water safety, added on water safety. Found voltage absorption system running weak, recommend repair. Found system low on r22, recharged system. Gave condenser coil a chemical wash and applied rust proof waxing. System operating at this time. Customer upgraded tune up to maintenance plan.
No cool upstair system. Find air condenser fail due to low charge. Find system leaking at loose service valve cap. Find system media coil rusted and can cause leak in future, need to keep check on system. Customer want to go with recharge and sealer HJ8B. Charge system to manufacture spec and add sealer to help stop leak. System operating at this time. Suggest plan and help maintain system and suggest to add performance enhancement upgrade to help system start up and reduce load.
No cool upstair. Find heatpump fail due to fault in voltage absorption system. Repair voltage absorption HN4A and system operate. Check and find system little under charge with r22. Find fan motor operating with high amp and worn. Find main electrical power switch pitted. Find airhanlder evaporator badly rusted. System have not water safety. Suggest customer to sign up for Comfortcontrol inc plan to help maintain system and keep check on system.
1 system ac tune up complete. thermostat is outdated, recommend replacing with newer, more reliable thermostat. Changed Filter. Recommend upgrading to 5 inch media filter to help reduce dust in house. Checked mechanical and electrical components, all in good shape. Gave condenser coil a chemical wash and applied rust proof waxing. Insulation on suction line outside was old and breaking down, cut it off and replaced it with new insulation. Recommend surge protection to protect unit from lightning strikes and power surges. System is slightly low on 410a, recommend recharge. Recharged system. system operating at this time.
No cool, check and find air condenser fail due to overheating. Find compressor overheat due to stress compressor and over amp. System run 15.6/13.5 rated. Coil very dirty and worn voltage absorption system. System is operating but not reliable and not efficient. System can fail at any time. Customer want to call Comfortcontrol Inc back for estimate to upgrade system. . Customer declined repair at this time.
Air Conditioning repair on Amana cooling system. Diagnose and perform annual AC maintenance service plan for residential customer. Clear drain lines and replace bad condensate pump on 8 year old HVAC system. Added R-410a refrigerant. Heating and cooling maintenance complete which will help lower cooling cost. Cooling system is now ready for spring and summer weather.