Excellent service. Always appreciate the folks at Comfort Control!
John is awesome.
Showed up on time did some troubleshooting tested the system and a tune up . Very fair price and the young service man was very nice !
Alex is the best Technician EVER! Very knowledgeable and great personality. He did a great job getting us up and running and we are VERY appreciative. You have a very valuable employee. Thanks again.
Thank you for quick, honest service on a crazy hot summer weekend!!
On time and fixed the problem quickly for a great price.
Gentlemen went right to work. Very polite and respectful. Made sure things were working correctly before leaving. Will use them again.
Jon Fowler called in advance, quickly diagnosed the issue, brought the repair option/cost to me, and then immediately solved the problem.
Awesome service. Technician very knowledgeable and pleasant.
My air went out and I did a quick online search. I found Comfort Control and was impressed by the 4.9 rating as well as all the great reviews. I can attest that they are all true! I was able to get same day service when others were booked out for weeks. The prices were reasonable and the service is impeccable!! Ricky was so personable and efficient.
Air Conditioning Replacement near Buford GA. Technician came out to install second AC unit and replaced current 6 year old unit.
10 year old Carrier Air conditioner is not blowing cool air. Technician performed Air Conditioning repair and maintenance tune-up. AC unit is now running properly.
A/c diagnostic in Buford. Replaced indoor unit main board, Bluetooth control. System has a bad 12 inch zone damper and needs a coil sensor/Plenum sensor. Provided quote to the customer for those items. Customer wishes to speak with Jeff Schmitt before agreeing to any more costly repairs.
Carrier Greenspeed 4 ton with zoning Supply Plenum 16" damper 12" damper Infinity zone controller Infinity UI Infinity zone sensor
Maintenance Buford. Did a leak search on evaporator coil. Did not find any leaks. Blower wheel is clean. Changed filter. Drain line is clear. No cracks in heat exchanger. Outdoor capacitor is within range. Compressor is good. Pressures are within range. System is cooling/heating at this time.
A/c diagnostic in Buford, unit is located in the crawl space condenser unit is old R22. Tempstar horizontal left hand 75,000btu 3ton slab coil with a 12â€ transition with metal supply, low voltage wire from unit to condenser needs to be replaced. Load center is Cutler-Hammer (pics attached).
Ac service in Buford. Discovered clogged drain line, furnace pan in horrible condition and needs to be changed, due to the age of the furnace replacement of it is HIGHLY recommended as well.
ECM condenser fan motor under part warranty. Rheem/Rudd. 15PJL36A01. Will be out of town until next weekend.
Replaced furnace control board. System operational at this time
Ac service in Buford. Discovered out fan motor failing, secondary motor weak and outside of manufacturing spec, system needs compressor saver to reduce stress on compressor, and system needs outdoor coil cleaned.
Ac service in Buford. Discovered loose wire in furnace preventing outdoor unit from coming on. Corrected and system cooling at this time
A/c diagnostic in Buford. 2 zones Unit located in the attic. System is cooling at this time, found zone 2 for the bedroom not operating properly and not opening. Found aluminum tape wedged in between the shaft not letting damper opening. Fixed problem, turned dampers OFF AND ON 3 times and they are now opening and closing at this time.
Ac service in Buford. Discovered dirty filter and weak blower motor controller. Removed filter and tested system operation. System operation normal at this time. Also discovered organic growth inside indoor unit. Recommend installing ultraviolet light system to combat organic and viral growth in system and throughout the home.
Ac service in Buford. Verified leak.
Complimentary duct cleaning