Chris was fantastic. Very knowledgeable and got my unit back going.
We were in the process of selling our home, our AC wasn’t working, I called Comfort Control and Chris came out that same day to find the problem. The problem was fixed in a timely manner. Costumer service from the office to the technician was great! Would absolutely recommend Comfort Control and will use them again as needed. Thank you!!!
Chris was great and knowledgeable
Prompt, knowledgeable, respectful and informative
Chris handle our annual fall service appointment with the patience and thoroughness we have grown to appreciate from the service tech's we've worked with over the 18 years we've been serviced by Comfort Control. I ask a lot of questions whenever a technician is in my home. This being now our second home that CC has provided service for, I feel good about the time taken to respond and educate me on HVAC topics and concerns. Chris easily met my expectations, again.
Christian was great! He knew exactly what he was doing and was very nice! I love comfort control, they really care about their customers!
We really appreciate our HVAC Tech Brian coming to our house so quickly. He dove right in and solved the problem we were having. He always answers any questions we have and explains everything throughly.
Jordan was punctual, and listened to our concerns.
Your tech was very friendly, and knowledgeable, he works in a timely manner. I would recommend him to all my friends and family members.
Took care of my issue quickly.
Free consultation Buford Georgia 30519
Furnace maintenance in Buford, Georgia. Two systems. Changed filters. Tested mechanical and electrical components. Found upstairs system with no water safety, dirty blower wheel, badly worn igniter, and worn flame safety sensor. Found downstairs system with badly worn igniter, worn flame safety sensor, and dirty blower wheel. Due to age and condition of furnaces, recommend upgrading them to more reliable, more efficient furnaces. Systems are heating at this time.
Renewing maintenance program in Buford Georgia. Completed the heating maintenance today . Checked the safety and performance. Checked integrity. Checked heating elements. Checked amps and motors . Changed air filter . System is heating at this time .
Free consultation Buford Georgia 30519 hvac new system installation
Pre sold repair in Buford. Arrived on site, replaced faulty heat kit, tested system, unit is operating normally at this time
Free consultation Buford Georgia mini split for basement
Giving a estimate on a maintenance program for 4 systems in Buford Georgia . Maintenance includes coming out twice a year . A heating visit and cooling visit . Checking the safety and performance. Checking integrity. Basic cleaning . Was not able to access roof ladder was not long enough. If Accent Fence wants to move forward will get the correct ladder to access the roof top . 3 package units and one hanging heater unit in the warehouse. Will send over price on the maintenance program. â€¢Signing Accent Fence up for the maintenance program. Going to get the ladder . Got a ladder to access equipment on the roof top . Completed heating maintenance. Checked the performance and safety of the equipment. Changed air filters . Checked integrity. Checked amps and motor . â€¢Workshop room . Has a bad ignition board would Recommend replacing that electrical part . Company doesnâ€™t use this system very much . Keeping that system off to prevent further damage to the equipment. â€¢Meeting
Pre-sold repair in Buford. Arrived on site, pumped down system and removed old evaporator coil, replaced with new aluminum coil. Pressure test and pull vaccum to 500 microns to remove moisture in refrigerant system. Charged to manufacture spec. Tested, system is cooling at this time. May need to come back in summer to adjust charge.
Main unit / not working / repaired main level/ performed 2 system maintenance in Buford
Heating issue in Buford Georgia. System was short cycling and tripping the high limit switch. Reset sensor and system is now heating and cycled system several times . Signing the family up for a maintenance program. Office will call and schedule first maintenance visit . Come out twice a year for a heating and cooling visit.
No cool in Buford. Arrived on site. Found heat kit only listing on one side. Split unit only able to keep up with the upstairs system. Will need to call Rheem in morning to find new 10kw heat kit
One system tune up/no heat in Buford. Arrived on site, found system fan continuously blowing due to tripped flame safty switch, reset and inducer motor came on, but pressure switch would not engage. Quoted for a bad pressure switch, but customer declined repair. Closed system up. System currently not operational.
No heat in Buford, arrived on site, found system fan constantly running with call for heat and no flame. Found zone board sending system into high limit in heat mode immediately upon startup. Determined cause to be faulty DATS. Disconnected from zone board and system started working. Will need to replace. Also found mold in system, recommend installing uv purifier to eliminate organic growth inside system
No heat in Buford. Check and find new zone panel was not set up properly. Set zone panel for second stage Aux heat with gas furnace. Tested control system and all 3 new nest tstat operating at this time.
No cool in Buford. Arrived on site to find system low on refrigerant due to leak in evaporator coil. Quoted to replace coil, collected payment and will be back to replace. System is heating at this time, but no AC.