Always professional and listen.
Vu Tran was very knowledgeable and very professional..
Reece was very knowledgeable and was very thorough with his explanation of services performed
Tech was excellent and informative very thorough.
Attention was nice, I wasn’t able to get everything I wanted done because it was too pricy. 264.00 to change a switch, another 200 to change a sensor. I was also not happy with the fact that I got charged 3% for paying with a card or I could pay with check. Who pays with checks now in days? Luckily I have one from like 10 years literally.
On reason I call Comfort Control first is the expert they send out to discuss the job, provide recommendations and a resolution. There is no sales pressure and we have a very comfortable discussion. The second reason is the service is exceptional and timely. All good
Heat pump maintenance in Buford Georgia. One system. Changed filter. Tested electrical and mechanical components. Heat strips not operating due to bad sequencer. Found evaporator coil corroded, rusty and dirty. Likely to leak and restrict air flow. Bad blower capacitor. Blower wheel dirty. Only one form of water protection and no emergency drain pan. Found bad capacitor on heat pump and overheating compressor along with probable refrigerant restriction as previously stated. Found electrical pitting on main electrical switch. Found line set insulation in bad shape. Due to age and condition of system recommend upgrading to a more reliable and efficient system. System is not operating properly at this time.
One system hvac tune up in Buford Georgia. Main level system. Changed filter. Tested mechanical and electrical components. Found evaporator coil to be rusted and corroded and likely to leak. System runs on R22 which is a refrigerant that has been phased out by the epa. System is from 2008. Due to age, condition, and lack of efficiency, recommend upgrading system to a more reliable and more efficient system. System is operating at this time.
Heat pump maintenance in Buford Georgia. One system. Changed filter. Tested mechanical and electrical components, all in good shape. Changed apco uv bulb. Flushed water heater. Recommend installing pureairx air purifier for improved air quality and pureairx electronic filter as well. System is heating normally at this time.
Heating maintenance Buford. Completed maintenance on 7 year old system. Air flow is slightly restricted from filter. Recommend installing electro static filter to better filter air as well as achieve optimum air flow. Combustion is good. Blower and coil are clean. Electrical components are working within range. System has no back water safety device to protect furnace from water damage. System would also benefit from having UV light treatment installed to kill bacteria viruses and chemicals in air that could cause harm to residents.
Heating tune up Buford. Completed tune up on 22 year old furnace. Blower is dirty ignitor is very worn. Flame sensor is good. Water safety switch working. UV light bulb needs to be replaced. Gas valve is leaking at shut off. Needs to be replaced. Gas line is not ran to utilize sediment trap. Need to re run to protect gas valve. System needs to be replaced due to age and repair price. Customer not interested in replacing at this time. Will cal back about repairs.
Heating tune up Buford. Completed tune up on 2 5 year old systems. Both heating good. All heating elements clean and within range. Blower and coil on both are very clean. Filters are good. Both systems have working water safety switches. All electrical components working in range. Both systems would benefit from having surge protectors installed to prevent smaller electrical components from failing. As well as downstairs system needs UV light like upstairs.
Furnace maintenance in Buford, Georgia. Checked all electrical and mechanical components. Found evaporator coil to be rusty and corroded and therefore likely to leak. Found dirty blower wheel. System has no water protection. System has no surge protection. Furnace is 21 years old , recommend upgrading system to a more reliable and more efficient system. System is heating at this time.
Heat tune up Buford. Completed tune up on 11 year old system. Inducer motor is failing. Bearings are giving out causing it to overheat. Roll out switches are rusted and could possibly stick when activated. Blower wheel is very dirty which is reducing the air flow a lot. Filter is good. Gas line is ran properly. Safety switch is working. Flame sensor ignitor and capacitor is good. Due to cost of repair and efficiency of system recommend replacing to a new furnace.
No heat Buford. Completed diagnostic. Found furnace with bad ignitor and flame sensor. Replaced both. System came on. Combustion is good air flow is good. Blower is dirty and capacitor is weak. System also has no secondary water safety device to protect furnace from water damage. System would also benefit from having air quality systems installed to better clean air and kill bacteria and viruses in air.
Heating tune up in Buford, Georgia. Two systems. Check all electrical and mechanical components. Found downstairs unit blower motor capacitor to be weak. Found downstairs unit blower wheel to be dirty. Found no water safety for downstairs unit. Recommend installing two forms of water safety. Downstairs unit not up to code . Has no drip leg on the gas line, and flexible gas line is being run into furnace. Found downstairs evaporator coil to be rusty and corroded, therefore likely to leak refrigerant. Due to age and condition of downstairs system, recommend upgrading system to a more reliable, more efficient system. Replaced blower capacitor for downstairs system. Systems are heating at this time.
No answer at the door
Heating tune up Buford. Completed tune up. Found 2 year old system running good. System is heating properly. Air flow is good blower and coil is clean. All electrical components are working good. System has no secondary water safety switch to protect furnace from water damage. System also would benefit from having UV light system installed to kill bacteria and viruses in air that could be harmful to residents.
Heating tune up Buford. Completed tune up on 2 2 year old furnaces. Downstairs furnace running good. With good air flow clean blower and evap coil. Changed filter. Safety switches working. Electrical components working properly. Upstairs system is all the same except air flow is very restricted. Not enough return air for the upstairs. Recommend adding return to computer room. Customer wants to do it. Will call to schedule.
Hvac tune up in Buford, Georgia. Three systems. Tested mechanical and electrical components. Found upstairs furnace with weak flame safety sensor. Found upstairs system with only one form of water protection. Found upstairs system with rusty, corroded evaporater coil likely to leak refrigerant. Upstairs static pressure is a little high on supply side, recommend changing registers out with high flow registers to reduce static. Found master bedroom system with weak flame safety sensor. Master bedroom system has a rusted, corroded evaporater coil that is likely to leak. Found main system with weak flame safety sensor. Found main system with rusty, corroded evaporater coil likely to leak refrigerant. Found main system with weak blower capacitor (5uf). Due to age and condition of systems, recommend upgrading systems to more reliable and more efficient systems. Systems are heating at this time.
Replaced inducer motor under parts warranty. System heating properly at this time.