Jordan was very experienced and professional will def use again!
Vu Tran is an awesome tech. He is nice and sincere and very knowledgeable.
Outstanding truly appreciate it
Vu continues to provide excellent service. Very professional, knowledgable and efficient.
Ta was very polite and did an excellent job servicing my heating unit. He made recommendations for when I would need to change my filter (wasn’t needed this visit). I definitely would recommend this company
System is extremely old and in poor condition. Need to replace. Please schedule Garrett for December 12th at 1pm
Two system tune up complete. Changed filters. Tested mechanical and electrical components. Found main level system with mold present, recommend uv lighting to kill mold, bacteria, germs and viruses for improved air quality. Found main level blower capacitor weak, recommend commend repair. Found upstairs dual capacitor weak, recommend repair. Systems are operating at this time.
Complete 2 heating pm check. Change both filter 16x25x1. Check safety and operations. Find upstairs heating 3 year old operating with in manufacturer spec. No concern at this time. Find downstairs heating system 16 year old operating with worn ignition, weak flame sensor and overheating resistor on control board and system very dirty.
Completed 2 system maintenance found upstairs blower dirty which will cause extra stress on motor and decrease air flow for the upstairs. Recommend cleaning to get proper air flow from system. Both systems missing secondary water safety switch. Recommend inline float switch to both systems to protect furnace from water damage and better protect house. Also recommend electro static filter for both systems to better filtrate air and keep systems and house cleaner longer.
2 system heating tune up complete. Changed filters. Dusted out furnace cabinets. Tested mechanical and electrical components. Found upstairs system with weak blower capacitor, recommend repair. Upstairs and downstairs systems both have mold, recommend uv light system to kill mold, bacteria, germs and viruses for improved air quality. Neither system has an overflow protection switch, recommend adding on to serve as backup to primary pan switch and to protect furnaces from potential water damage. High static pressure is present in both systems. Recommend less restrictive electronic air filters. Customer upgraded tune up to maintenance plan. Replaced upstairs blower capacitor. Installed pureairx bronze package in both systems. Systems are heating at this time.
Heat pm. Discovered upstairs furnace Locked our on pressure switch. Cleaned port and furnace is operational. Main level system has high oxygen and high carbon monoxide output and needs to be calibrated. Ductwork on Both systems are extremely dirty and need duct cleaning. She wants to finance
Complete 1 system furnace repair and preventative maintenance check. Changed 5kw heat strips to 8kw and did comfort bridge installation set up.
Complete 1 system furnace repair and preventative maintenance check. Complete heating pm check. Change filter, check safety and operations. Find heatpump and Airhandler operating within manufacturer spec. No concern at this time.
Complete 1 system furnace repair and preventative maintenance check. Found thermostat was bad. Replaced and restored heating and cooling.
Complete 1 system furnace repair and preventative maintenance check. Discovered bad igniter and worn flame safety. Changed both. System heating at this time.
Complete 1 system furnace repair and preventative maintenance check. found static pressure good and combustion readings good. Changed media filter. All electrical components good and working safety features.
Complete 1 system furnace repair and preventative maintenance check. Installed inline safety switches on both drains in the attic. Quoted to do fresh air return with air purifiers and filtration on both systems.
Complete 2 system furnace repair and preventative maintenance check. Change upstairs filter customer provided. Did not change the downstairs filter. Check safety and operations. Find both heating systems operating within manufacturer spec. No concern on both furnaces.
Complete 1 system furnace repair and preventative maintenance check. Changed filter. Ran static pressure test, the pressure did not exceed system max rating. Ran combustion analysis, CO levels are low and O2 levels are within range. Tested all electrical and mechanical components, all readings are nominal.