Reece arrived at my home shortly after I contacted him about a problem with my furnace. He diagnosed the problem and made the necessary repairs. Now I'm cozy warm again! I recommend this company and this serviceman.
Complete 1 system a/c repair and preventative maintenance check. Find the cooling system operating but has worn/stress compressor. System fan motor operating with high amp and leaking oil. Need to keep a check. System operating at this time. Note: customer said some time house get to 72 degrees but house set for 77. Check both zones but did not detect problems.
Bad condensate pump, replaced under warranty.
Renew Comfort Club Membership and Complete 1 system repair and preventative maintenance check. Did not change the filter. Replace #35 water panel. Find furnace operating with manufacturer spec. Suggest apco air purifier to help improve air quality and prevent molding. System operating at this time.
Complete a/c repair and preventative maintenance check. Found 18 year old Carrier a/c unit operating with stress compressor, worn and using high level of power, evaporator coil in crawlspace and dirty, system operating at this time. Replace filter and install hard start kit.
1 system a/c repair and tune up complete. Changed 14x25x1 filter. Tested electrical components, all in good shape. Chemically washed condenser coil. Found system a bad txv not properly metering superheat, recommend repair. System is operating at this time.
No heat furnace repair call. Found clogged Beckett tubing. Cleared tubing. Changed Aprilaire 610 filter. Changed blower motor capacitor (5uf). Found water heater leaking, due to age and leak, recommend replacing the water heater. The system is heating at this time.
No heat. Check and find 3 year old carrier furnace operating normal. Find condensation pump full of water and tubing frozen clogged drain. Remove 3/8 tubing and replace condensation pump with new tubing and run drain to main house drain line to prevent freezing and wire up water safety. Repalce dirty and molded water panel #35. Replace dirty filter with AA810. Sign up 1 CCI plan and complete heating PM check. System operating at this time.