Response from Comfort Control Heating & Air:
We thank you for sharing your positive experience during your HVAC Service.
Response from Comfort Control Heating & Air:
Thank you so much for your 5-star review! We will share this with the team to let them know to keep up the amazing work.
Very nice young man, friendly,Helpful with our questions & explanations . Through job with install and clean up and everything was very satisfactory . Thanks for such a quick response and install. Water heater was at a point it could have opened open and poured out the water. We only moved in three months ago and you have already resulted two major problems in our new residence. Thanks so much!
Young man is outstanding
Brett provided great service and was very thorough
Jordan was professional, courteous, very knowledgeable about heat pumps, and arrived ahead of schedule! Agreed to 3 of 5 servicing items. Prices on 3 items seemed reasonable after discounts. Opted not to get the $1,400 ultraviolet system to prevent organic matter presence and was not offered any alternatives or how to self-clean. Company needs to revise the 'system check form' to properly annotate combustion checks do not apply to heat pumps. Otherwise, pleased with first service call with Comfort Control.
I am a real estate agent and needed a HVAC company to come out the same day to look at the unit on my seller’s home which we were closing on the next morning. Reece came out within 1 hour and fixed the issue for a great price. I would definitely recommend Comfort Control Heating and Air to anyone needing fast, reliable service at a great price!
Would definitely give a share with others😊
Went to a customer's home to provide summer maintenance on their air conditioning system. Checked all electrical connections, changed the air filters and checked the system's charge. The unit is operating as the should.
Installed a new air conditioning system for a residential customer. Replaced the old system with a Ruud 3-ton condenser, coils, heater, and thermostat. Showed the customer how to work the new thermostat and made sure the whole system was working properly before leaving.
Went out to perform annual maintenance on a customer’s air conditioning system. Checked the system for signs of wear and tear. Replaced filters, but found no other issues. The system is working well and ready for the summer.
Went out to a scheduled installation of a new air conditioning system. The customer's current system was original to the house. Removed the old system for them. Tested the new one for quality and operation. The customer was pleased with the service.
Install in-house WiFi thermostat.
Service call in Buford. Changed filters on all 3 systems, UV bulbs are not the ones we have. UV Bulbs need to be ordered. All 3 systems are cooling at this time.
A/c diagnostic in Hoschton, system is not cooling properly, blower wheel is clean, evaporator coil looks good. Filter is clean.
Actually service in Hoschton. Discovered compressor blow terminals and is leaking refrigerant. System under warranty for outdoor replacement and ordered.
Ac service in Hoschton. Discovered system running with a 27* superheat, extremely rusted coil, blower motor leaking oil, water in furnace, outdoor air electrical switch starting to burn and becomes pitted. Due to age, compressor and type of refrigerant, replacement is HIGHLY recommended.
Year old Daiken system is not cooling, found the EEV valve to be stuck and not allowing enough refrigerant through. Unstuck valve and system is cooling with a 18Â° split. If issue persist the EEV valve will need to be replaced. Brought subcool up to 9Â° and superheat to 22Â°.
A/c diagnostic in Hoschton. Indoor unit is in the attic. System is cooling at this time. Fan speed is on high, filter is clean. Outdoor condenser is clean, had to adjust pressures and they are good now. Thermostat is set to 74Â° and room temperature was at 76Â°. With testing unit temperature went up to 78Â°. Did more diagnostic testing on the unit and everything is working properly at this time.
A/c diagnostic in Hoschton. System is not turning ON. Unit has no refrigerant at all, found leak in the evaporator coil. Evaporator coil is covered under full warranty.
A/c diagnostic in Hoschton. Unit had a really dirty filter, restricting airflow through the coils making it ice up. Last time we were out from the work performed in the history, is ( 8-1-20 )
No cool Hoschton. Completed diagnostic. Found system with completely clogged. Changed filter. Found no leaks in coil. Furnace is clean and all components inside and out are good. Pressures are good. System cooling at this time.
Ac service in Hoschton. Discovered failed outdoor temp thermistor. Order from east coast Suwannee