Chris is friendly and courteous. He knows how to operate our system and indeed he can explain it to us satisfactory. We struggle with changing the system, particular from one season to another. Nevertheless, Chris explains it in such a way that we understand!
On time, respectful, Very friendly great Coustomer service, due to service provided by tech I will recommend company and use again.
James showed me where the furnace had NOT been replaced a few months ago by a different company. I pd. for a product that had not been installed which is a travesty. He also pointed b out some wiring that was not to code.
He was very professional
Jon was timely, professional in his review. Wore booties and mask and maintained social distancing during the service call.
On time, efficient & great Tech!
As usual great service. John took the time to answer all of our questions.
Reece was on schedule in fact early and solved my heating issue in short order. He was very courteous and helpful.
â€¢Dropping off filters. Changed out fresh air X filters for all 3 systems . Left a box upstairs in the attic and basement . Left box supply of filters .
HVAC issues in Hoschton Georgia. Warranty System is taking to long to heat house and not getting to asking temperature. Looking into that issue now . Checking settings and controls . Running several test on the equipment. Set up several dip switches. Put system in a test cycle . Also today had to charge system to speck levels and will recheck pressures in the summer to make sure they stay stable . Had to also recalibrate the thermostat. System is heating now .
Customer concern in hoschton. Arrived on site, customer complaint of unit running longer than they think it should. Explained that they have a steam humidifier and that it was trying to satisfy humidity in the house. Humidity set to 45% and it was only at 43% uppon arrival. Set humidity control to 40% to try to eleveat run time. Unit is operating normally at this time.
No heating main level in Hoschton. Check and find main level furnace ignition fail. Replace ignition and complete combustion calibration service for Lennox furnace. System operating at this time.
Looking over air quality in Hoschton Georgia . Found the air handler does have biological growth growing in the system . Took pictures and videos . Found the growth growing on the drain pan for the Evap coil . Found the biological growth growing on the air handler doors and on the wiring . Biological growth is on the condensation drain line on the pee trap . Going to be giving the family some solutions on how we can create cleaner air and get rid of the biological growth. Would also recommend putting a vent on the drain line with it being in a attic . Family is going with the recommendations on improving the air quality. Going to complete as much as I can today and the rest tomorrow. Will collect half today and the rest when the job is completed. Today I completed the rest of the air quality repair . â€¢Completed heating maintenance. Checked safety and performance. Checked heating elements. Checked integrity. Checked heat pump . Checked heat kit . Completed maintenance cleaning. Sy
â€¢Completed heating maintenance Hoschton Georgia . Checked the safety and performance. Renewal visit today . Checked the integrity of the heating operation. Checked heating elements. Changed air filter 16x25x1 . Tested zone dampers . System is heating properly at this time . Total amps on furnace are at specks . â€¢Recommend some form of air filtration device with a UV light to kill and prevent biological growth and to keep the system clean and add longevity to the equipment.
Heat pump maintenance in Hoschton, Georgia. Deaton Creek. One system. Changed filter provided by customer. Tested static pressure. Tested mechanical and electrical components. Discovered pitting on main electrical switch, recommend replacing switch. System has no surge protection, recommend installing surge protection to protect equipment from power surges. System is heating normal at this time.
â€¢Completed a two system tune up in Buford Georgia. Checked the performance and safety of the heating operation. Checked heating elements and amps on motors . Checked integrity. Changed air filters . Equipment is from 2005 . Equipment is 15 years old . â€¢Main floor furnace has a weak ignition and has silca build up would highly suggest replacing that electrical part to prevent future issues with the heating equipment. â€¢Main floor has a rusty R22 coil that could eventually lead to R22 leaks . Took pictures. â€¢Would recommend the water safety mechanics be upgraded To a water pan switch. â€¢Flame reader wire terminal shows signs of burning the terminal and the insulation. Would recommend replacing the wiring for that electrical part. â€¢Main floor has a weak blower start cap that runs and starts the blower would highly recommend replacing the blower start cap to prevent future break downs. â€¢Main floor is heating at this time but would recommend the repairs above. â€¢U
No heat in hoschton. Arrived on site, found bad comfortnet thermostat. Swapped face out under parts warranty. Unit is operating normally at this time
Free consultation for ductless mini split.
â€¢Completed heating maintenance in Hoschton Georgia on 2 mini split systems. Checked the safety and performance of the heating equipment. Checked heating elements. Changed air filter 20x20x1 . Flushed drain line and added a union for easy service on the drain line . Checked the integrity. Renewing the maintenance program today . UV lights are working properly. Heating equipment is working properly. Thank you .
- Completed a two system heating maintenance in Hoschton Georgia. Prepaid visit today . Checked the heating operation. Checked heating safety. Checked heating elements. Changed air filters . â€¢Main floor furnace. Has build up and debris on the blower wheel which is causing stress to the motor and taking about from performance/ air quality. Would highly suggest having the blower housing and wheel cleaned and deep chemical washed . â€¢Gas line is not code for the main floor furnace. Would highly suggest bringing the gas line up to code . â€¢Basement furnace has a clogged inducer port and needs to be pulled out and cleaned and the Bvent has particle and debris in it . You can hear it getting thrown around when the inducer is running . Family is going to call the company that put the Bvent in and see if they will cover it .
One system heat maintenance in hoschton. Arrived on site, changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Unit is operating normally at this time. Suggest installing uv air purifier to system to improve indoor air quality.
Heating maintenance Hoschton. Completed maintenance on 13 year old furnace. System is running good. Blower and heating elements clean. Tightened all connections. Safety switches working. Combustion is good. Gas line not ran properly to utilize sediment trap. Need to re run pipe to allow full use of trap. System would also benefit from having electro static filter and UV light treatment installed to better filter air and kill bacteria and viruses that could cause harm to residents
One system heat maintenance in hoschton. Arrived on site, changed filter and cleared barometric ports. Checked ignition systems, electrical connections amp draw and capacitance. Found system constantly running bec thermostat humidity control was on , but humidifier was off. Turned on humidifier and system started working properly. Recommended installing surge protector to unit. Installed surge protector. System is operating normally at this time