AC pm check complete. Left customer with replacement filter. Cleared drain line and added chlorine tablets to evap coil drain pan. Checked mechanical and electrical components, all in good shape. Gave condenser a chemical wash and applied rust proof waxing. System operating normal at this time.Found system undercharged on r22, recommend recharge.