No cooling in Jefferson, GA Heat pump unit freezing up due to no air flow at the indoor unit. Found blower relay meted at the terminals causing no voltage to the blower motor. Relay needs to be replaced and wires repaired. Bypassed relay to run blower constantly, until relay can be replaced. Checked charge on outdoor unit to find it slightly low on refrigerant. Leak searched indoor coil and was not able to find a leak. Possible incorrectly charged from another company. Corrected charge. Will return with the relay to make proper repairs.