The technician was knowledgeable and great to communicate with.
Christian was professional and took care of our problem and explained everything. Great service both times I had an issue.
Jordan was very patient and informative. Spent time explaining the problem.
Ac maintenance in Roswell, Georgia. Three systems. Did not change filters. Tested mechanical and electrical components. Found main system with weak dual capacitor (45/5 mfd). Recommend repair and install of hard start kit to reduce load on compressor so it starts smoother, runs smoother and therefore lasts longer. Upstairs dual capacitor is weak as well (35/5 mfd). Recommend repair and hard start kit. Replaced dual capacitors for main system and upstairs system. Installed hard start kits on all three systems. Systems are cooling at this time
Ac maintenance in Roswell, Georgia. One system. Changed filter. Added chlorine tablets to condensate pump. Tested mechanical and electrical components. Found system with weak blower capacitor (7.5 mfd). Recommend repair. System has no emergency drain pan or water safety. Static pressure is high due to undersized ductwork. Refrigerant pressures are good. Did not wash condenser coil at customerâ€™s request. Pad underneath condenser is broken and unit is i level. System is cooling at this time. Renew 1 system cci plan.
HVAC tune up in Roswell. Tested operation of 1 system. Discovered burnt and pitted main electrical switch. All other components tested within normal manufacturing spec. Outdoor unit needs cleaning. Recommend ultraviolet light system to combat organic and viral growth in system and throughout the home. System heating and cooling at this time. Signed up for maintenance membership and cleaned outdoor unit
Ac maintenance in Roswell. Tested operation of 1 system. Discovered compressor hard start weak and outside of manufacturing spec. Needs replaced. System also needs a duct cleaning and recommend surge protection for indoor unit. System operation normal at this time. Replaced hard start.
HVAC inspection in Roswell. Tested operation of 1 system. Discovered furnace having issues igniting. Ignition has heavy signs of wear. Flame safety has signs of wear. Chamber extremely rusted, blower wheel is dirty, inducer motor bearings are worn out and grinding, old furnace flue pipe is not properly capped off and is still being used for water heater exhaust, gas line is not hard piped into furnace per code, condensate vinyl tubing is extremely corroded, starting to leak and in danger of complete clog which best option to replace would be through exterior wall in garage, ac secondary controller is weak and outside of manufacturing spec, system needs compressor saver to reduce stress on compressor and help with start up, outside control wiring is exposed to the elements at connections and is corroding, outdoor fan motor is over amping and pulling too much electricity, systemâ€™s coil is very dirty and needs to be cleaned, refrigerant line insulation is missing in some spots outside,
No heat in Roswell. Check and find 16 year old rheem system. Find gas furnace not operating properly due to fail flame sensor. Replace flame sensor and blower motor capacitor. System operating at this time. Sign up 1 comfort control care club. Need to schedule for June to do cooling maintenance and October for heating maintenance. System operating with dirty blower assembly, minor rust on Evaporator coil, ac unit operating with dirty condenser coil and missing hard start kit. Give customer estimate for additional work need to system. Per service manager, waive service fee. Customer approved repairs and credit card charge over phone.
Free consultation Roswell georgia 30075 hvac furnace A/C
Heating maintenance in Roswell. Discovered upstairs system with ignition starting to show signs of wear, dirty blower wheel, dirty ductwork, early signs of organic growth, coil is extremely rusty and leaking refrigerant, blower cabinet rusted out. System is extremely old and past itâ€™s expected efficient life span. Replacement is HIGHLY recommended. Downstairs system has dirty blower wheel, dirty ductwork, rusted and leaking coil and the ignition also has signs of wear. System is also past its efficient life span. Replacement is HIGHLY recommended. Basement system has dirty blower wheel and rusty coil. All systems heating at this time
One system tune up in Roswell. Arrived on site checked filter and cleared barometric port. Checked ignition systems, electrical connections, amp draw and capacitance. Found system with overflow water safty switch, but no primary wet switch, no aux drain pan and a dirty blower assembly, should be pulled and cleaned. Recommended installing surge protector to each piece of equipment, a compressor assist kit to outdoor unit to prolong the life of the compressor, and a uv purifier to improve indoor air quality. System is operating normally at this time.
One system tune up in Roswell. Arrived on site, checked filter and cleared barometric port. Checked ignition systems, electrical connections, amp draw and capacitance. Found system with overflow water safty, but no primary. Recommended installing surge protector to indoor and outdoor unit, and a compressor assist kit to prolong the life of the system. Unit is operating normally at this time.
HVAC home inspection Roswell Georgia. Tested operation of 2 systems. Upstairs furnace ignition has heavy signs of wear. All other components tested within normal manufacturing spec. Furnace is a 2018 Model. Air conditioning has a 20 degree split between return. Outdoor compressor starter and secondary controller are out of manufacturing spec but still functional. Replacement of components are recommended. Ac is a 2011 model Downstairs furnace ignition also has heavy signs of wear. All other components tested within normal manufacturing spec. Furnace is a 2011 model. All ac components tested within normal manufacturing spec. Ac is a 2017 model. Both systems heating and cooling at this time. Downstairs system would greatly benefit from compressor saver hard start kits to reduce stress on compressor and reduce energy consumption on start up which will extend the life of the system. Both system would greatly benefit from ultraviolet light systems to combat organic and viral growth in syst
Heating repair in Roswell. Homeowner Stated that after changing his thermostat the new one was not receiving any power. Discovered a blown fuse on electrical board. Changed out fuse wired and thermostat and system to run witnessed. Was not enough wires so homeowner opted to have no fan feature. Tested heating and cooling both operational at this time.
No heat in roswell. Arrived on site, found main level furnace not functioning. Found control board sending voltage to inducer motor, but motor is not operational. Quoted price for new inducer motor, but due to age and condition of unit I recommend replacing equipment. Unit is not operational at this time
Heating maintenance in Roswell. Tested operation of two furnaces. All components within furnaces tested with a normal manufacturing spec. Systems really need a duck cleaning and ultraviolet light system to combat organic and viral growth in the system and throughout the home. System does not have any drain line water safeties to help prevent flooding in the attic due to common drain line clogged. Systems heating at this time