Timely, courteous, friendly, knowledgeable. Comfort Control is an outstanding HVAC company. I highly recommend them!
Called office after hours. They were out at my house the very next day. Courteous, Dependable, Knowledgeable. Strongly recommend this company!
As always, the technician Vu did a great job!
Steve came-out late one evening (on-time) reviewed the issue and proposed a solution. Repair timing was scheduled - price and timing was met. In addition, Steve reviewed a previous issue and made an adjustment. Comfort Control is the only company we used in past 10 years. Value and meeting commitments are 2 important reasons!
Our unit is 20+ yrs old. Steve found a short some place in the AC and got it working but for how long ?!?! hah. Needless to say we are getting a new unit put in ASAP.
Have used Comfort Control for years. Very satisfied with their skilled service!
We purchased two entire furnace and AC units less than 10 years ago. Our maitenance and repair cost (required and suggested) since the installation is in the thousands of dollars. We replaced original working units primarily based on "efficency gains sold to us". This has been a dissapointment from a costs perspective.Technicians are always knowledgable, timely and polite.
Completed 2 system furnace repair and preventative maintenance check.
Completed 3 system furnace repair and preventative maintenance check. Renew Comfort Club Membership. Did not change the filter. Customer have electric air cleaner. Find both systems operating within manufacturer spec. System operating at this time.
1 system furnace repair and preventative maintenance check. Replaced filter. Recommend inline safety switch for the drain. The system is running at safe levels.
1 system furnace repair and preventative maintenance check. Replaced filter. Adjusted levels. Found furnace running higher CO levels. Recommend inline safety switch for the drain line.
Repiped stove gas line and replaced gas cock. Installed a drip leg on furnace at no charge. Should have been done on the insulation.
Complete 1 system repair and preventative maintenance check. Change filter, find system operating within manufacturer spec. System operating at this time.
Found pilot light not lit. Relit pilot light for customer.
Performed prepaid heating maintenance on two rooftop units. Changed filters. Spoke with owner's wife about the blower motor cleanings and they said they would have to call back.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at email@example.com or call us at (770) 932-5012.
Check on system. Found system cooling normal. Needs zone system to regulate system.
Renew and complete a/c repair and preventative maintenance check. Change filter, check drain and clean a/c coil. Find the 10-year-old system operating normally. Suggest compressor hard start kit to improve start-up and reduce the load. Customer declined at this time. System operating at this time.
Replaced rescue motor with OEM CFM. The system is cooling well at this time.
Found CFM bad. Weak Capacitor and pitted contactor. Replaced all parts and restored cooling.
2 system a/c repair and preventative maintenance check complete. Cleared upstairs drain line. Added chlorine tablets to condensate pump. Tested systems and found upstairs condenser with a pitted voltage distribution system, recommend repair. Replaced upstairs voltage distribution system. Found both compressors operating at high amperage due to age and wear over time. Recommend hard start kits to take a load off of compressors to help them start and run smoother and prolong the life of the systems. Systems are cooling at this time. Recommend surge protection to protect units from power surges.
Completed a/c repair and preventative maintenance check. Replaced customer supplied filter. Cleared drain. Amps and pressures are good. The system is cooling well at this time. Recommend a Surge protector and APCO UV.