Very nice yet professional. Told us options for possible repairs, but was not pushy.
The technician was professional and took the time to explain the issues. My unit was fixed and cooling in less than an hour.
Fast, professional, quality and reasonable!
The technician was on time and professional. Offered a few options to fix my problem and other services that the company offered.
Our technician was Chris Southerland. He was extremely professional and respectful of our home. He worked quickly to identify the problem and repaired it just as quickly. Thanks to Chris we have a nice cool home again!!!!
Reece was very professional, cared for our needs, and very informative about what we needed to have done.
Very professional and friendly!
Well done, timely but forgot to put on mask.
Two system heat maintenance in sugar hill. Arrived on site changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Recommend installing secondary water safty switch to each system and surge protection to protect electrical systems. Both units are operating normally at this time
Heating maintenance sugar hill. Completed maintenance on 4 year old furnace. Furnace is heating. Changed filter. System has only one form of water safety. UV light will need to be replaced in spring. All electrical components are good. Heating elements are good. No sign of rust or over heating.
Heating tune up sugar hill. Completed one system tune up. Found furnace heating properly. All heating components working and clean. All safety switches working. Zone board working with its own transformer. Gas pipe ran properly. Insulation is good. Filter is good.
Heating maintenance in Sugar Hill. Tested operation of 2 furnaces and 1 heat pump. Discovered upstairs flame safety testing outside of manufacturing spec. All other components tested within normal manufacturing spec. Recommend ultraviolet light system for basement unit for mold prevention. Replaced upstairs flame safety. Systems heating at this time
Heating maintenance in Sugar Hill. Tested operation of two furnaces and one heat pump system. All components on furnaces tested within normal manufacturing specs. Need ultraviolet light system to combat organic growth inside units to maintain indoor air quality. Basement system is struggling to Heathâ€™s spoke with homeowners and they are remodeling the basement and are probably going to replace it during that process. Renewed membership for 2 systems
Three system heating maintenance in sugar hill. Arrived on site checked filters and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Recommend installing secondary water safty for each system to prevent damage to electrical systems, as well as surge protectors. All systems are operating normally at this time.
Ac repair in sugar hill. Discovered batteries dead in bonus room thermostat. Replaced batteries and system started cooling again. System cooling at this time.
Heating maintenance in Sugar Hill, Georgia. Two systems. Changed filters. Tested mechanical and electrical components, all in good shape. Systems are heating normal at this time.
â€¢Completed heating maintenance in Sugar Hill Georgia . Checked the safety and performance of the heating system . Checked integrity of the heating elements. Checked amps . Checked air quality. Filter size is 20x25x4.5 will need to order filter and when it arrives at the shop will come and replace air filter . Prepaid visit today. System is heating at this time . â€¢Sediment trap is not code for the gas valve would highly recommend bringing that up to code. â€¢Air movement system has lots of particle build up which is causing a decrease in air quality and making blower work harder would highly suggest having the air movement system pulled out and deep chemical washed . â€¢Would recommend a secondary water safety device to prevent water damage to the equipment. â€¢Today I wiped off some biological growth on the equipment with some disaffect whips . Would highly recommend a UV light in the system to kill and prevent the growth from getting into the air stream .
Heating maintenance in Sugar Hill. Tested operation of 2 furnaces. All components tested within normal manufacturing spec. Ultraviolet bulbs will need to be replaced in the spring. Systems heating at this time
Ac repair in Sugar Hill, Georgia. Replaced upstairs heat pump under unit replacement warranty. Warranty for this unit goes into the existing warranty. Pressure tested and flushed system with nitrogen. Pulled a vacuum to 500 microns. Charged system and it is operating at this time. Customer used $50 gift card
Water leaking from ceiling in Sugar Hill, Georgia. Found water stain next to vent stack in attic, leak has nothing to do with hvac. Recommend calling roofer.
Heating maintenance sugar hill. Completed 2 system maintenance. Main floor is new furnace with good combustion. Filter is good. Blower is clean. All safety switches work. Both systems would benefit from having UV light installed to kill bacteria and viruses that could cause harm to residents.
Heating maintenance in sugar hill. Tested operation of 1 heat pump. All components tested within normal manufacturing spec. System would greatly benefit from compressor saver hard start kit to reduce stress on compressor and reduce energy consumption on start up which will extend the life of the system. Also ultraviolet bulb needs to be replaced. Added compressor saver to system. System heating at this time
Heating maintenance in sugar hill. Tested operation of 1 furnace. All components tested within normal manufacturing spec. System operation normal at this time