Very knowledgeable of this system and thorough Thank you
The entire staff at Comfort First is both courteous and helpful. Their technicians are professionals. What a pleasure to be associated with such a superior customer service oriented company. Well done Owners !!!
Young man was very professional and intuitive. His explanation of my system was detailed. I would hire him or promote him immediately.
I was very pleased with the repairman.
always great service ty
Quick diagnosis and repair.
Great service. Professional and knowledgeable
Professionalism: Eric is an outstanding professional. Problem Resolution: Problem has been resolved "for now'. Replaced a motor and capacitor. Timeliness: Eric arrived at about 2:50PM this afternoon. Very early into the 4-hour service window provided by Comfort First. Appreciate you all.
I'd like to say a big Thank you to Andy, he was excellent, friendly and efficient. We even talk about winterizing the unit. If I do I'd like him to do the job. Thank you Comfort First.
Working on rheem gas furnace
Complete: EPA Maintenance: Payne Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
clean outdoor coils on Goodman heat pump AC split system and checked refrigerant pressures
Working on amana gas pack
Incomplete: came to look at duct work under home. First section near crawl space door all looked intact. At the main truck line all looked good as well looking from left to right. However on the far rt hand side it seems one of the supply lines has been knocked off the boot by fallen insulation or some other cause. Beneath that supply line there are bubbles coming up from the insulation and standing water beyond that. Appears to be a broken washing machine line or something to that effect according to the smell. We cannot do work until that area is dried up and leak fixed. We will need about 25’ of flex to repair line and attach to the boot. At that time we will also be able to see beyond the main trunk to see if there are anymore issues. That section blocks access to look at remaining supply lines. Need to call property manager and let them know our findings. I tried to call but could not get through. 25’ of flex needed for repair. Pics in Docs.
lite pilot light on Gibson gas furnace
Complete: 1 System: Goodman split Heat Pump: Added 2lbs of r22, hard start and leak stop. Let it run for 15-20 min System is older but is running good at this time.
Working on lennox heat pump.
performed leak search on trane gas pack
Working on goodman heat pump.
Found bad blower control board on ICP gas pack
Working on general electric furnace
replaced capacitor on Bryant heat pump AC split system and clean drain line
Completed heating maintenance on Goodman gas furnace