Billy fix the problem in our system in short time, even it was not easy to access to it. Thank you!
Excellent customer service, friendly, prompt , and professional
Billy was kind , courteous, and knowledgeable. He showed that integrity still exists in customer service!!!!!
Billy and Brad did a fast service and they were both professional and corteous.thank you!
Air has shut on and off multiple times. Tony immediately know where the problem was. Replaced switch...thermostat came on... I have air! Friendly great service, Thank you
Travis went right to work and did a great job. He took time to answer questions and explain the work done...as well as giving us things to consider if a similar issue arises. Great guy and very professional. Any company should be proud to have a representative like him.
Terry was the best technician that has ever been to my home. He was professional. He showed me what the technician did wrong from Advanced. I will never use another company and I will always ask for him. My unit is two times better. He set my controls on 70 and my home is warmer than 72 where i had it set. Thank you Mr. Terry. Advanced told me that I needed a capacitor and he just had to wire it correctly. And made changes to my gas flow because it was incorrect. He made a liar out of them. It’s working correctly. It is cozy in my home now.
Terry was bye far the best technician I've ever had. Knowledgeable and friendly. Best of all he fixed my heater and taught me what to look for. I will definitely use this company and request Terry for all my heating and cooling needs from here on out. Highly recommended!
Goodman gas furnace found no issues checked all mechanical and electrical components
Goodman gas furnace replaced inducer motor
Amana gas pack preformed heating maintenance
Amana gas furnace preformed heating maintenance
Trane heat pump checked system found to be low in refrigerant and added 1 lb R-22 to system and cycled system working at this time
Coleman air handler checked system found zone control board set for gas and reset control board and cycled system working at this time
Trane furnace check
Goodman gas pack replaced draft inducer assembly and cycled system working at this time
Goodman gas furnace replaced blower motor and capacitor and cycled system working at this time
Godman gas furnace replaced control board and cycled system working at this time
Comfortmaker gas furnace checked system found open pressure switch due to draft induce motor not running due to being bad need to replace draft induce assembly
Goodman gas furnace checked system found blower motor nit running due to being bad need to replace blower motor also checked 2nd system and found dirty flame sencer and cleaned and cycled system working at this time
Trane heat pump checked system found defrost sence not properly mounted and repaired and cycled system working at this time
Lennox gas pack replaced blower relay and cycled system working at this time