Assigned Comfort First by my warranty service. Prompt and professional service. David took time to explain the issue, repairs and answer questions.
I would recommend this company and Thomas to anyone
Quick and on point
Trust worthy and professional company. Technician was very professional and thorough. He explained everything he was doing as well as what he found. I am very satisfied with my service experience.
Cody Smithwick did an awesome job, very professional and knowledgeable. ☺️
Cody came and listened to our problem and in no time resolved the issue. Awesome.
Great company and great customer service I am very happy and the house feels so much better thank you!
He was awesome and took his time explaining things and answering questions.
Complete: 2 Systems: Worked on Downstairs Unit: Trane Split Heat Pump: HO said it just stopped working and sound outside as if it was trying to run but would then click out. Opened HP and saw swelling on the capacitor. Changed Cap and system and Charge looks good and running great at this time!
Complete: 2 Systems: Worked on Upstairs Unit: Payne Split HP (NO DATA PLATE) r-22 refrigerant. Homeowner said it would work for a little while and then it would start blowing hot air turn the system off turn it back on nothing would happen couple days go by turn it back on and it would start working again. At the heat pump checked pressures pressures looked good checked the amp drawls the amp drawls looked OK. Difficult to know exactly where it needed to be. Check the capacitor and the common wire from the contactor to the capacitor was barely touching And the capacitor was bad. Replaced capacitor and tightened wires. 20° temperature split upstairs. System looks good and running great at this time!
Performed leak search on Goodman heat pump AC
Performed diagnostic on Goodman heat pump AC
Performed preventive maintenance on Goodman heat pump AC
Performed preventive maintenance on Amana heat pump AC
Replaced condenser fan blade on Goodman heat pump AC
Replaced condenser fan motor on Lennox heat pump AC
Performed diagnostic on Goodman heat pump zone board
Completed load calculation for a customer who is intrested in having their system replaced and getting Duke Energy rebates.
Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils
Completed load calculation for a home warranty customer to have their system replaced.
Replaced compressor on Payne split heat pump
Complete: 1 System: Goodman Split HP: Tenant said unit was working intermittently blowing out cold air. At HP found contactor pitting and melted plastic keeping contactor from making connection all the time. Replaced contactor checked refrigerant and system is working great at this time.