Did great job replacing heater and coils. Also quick to respond and has customers needs at heart.
Awesome company. Came the same day I called. Found motor bearing going bad, but didn't try to sell me a new motor. Suggested I wait to replace motor when bears failed completely or in springtime when I would need the motor working perfect.
Great company always helpful and responsive. Someone I can trust for a good assessment of what needs to be done with out up-selling me on replacement units or expensive "repairs". They will let you know what needs to be done even if that is a simple maintenance where they won't need to come out.
James and his team were great, quick and effective!
This gentleman runs his company the right way! He values customer trust & satisfaction over personal gain.
I would recommend company to anyone.
Service call that the heater for the downstairs is not working. Find the circuit board and relay on the strip heater burnt. pick up parts at Carrier and replace. This unit is working well.
Service call for a service and check up. The amp draw on the compressor and motors are all within specs. The freon levels on this heat pump are within specs. This unit is working well.
Service call that the outside unit is making a loud noise and the fan is not turning. Find the condenser fan motor locked up. Replace the condenser fan motor and start the heat pump up. This unit is working well and the family will be warm for the winter.
Service call to service and check to ac and heat systems and change out two thermostats. The systems are working within specs.
Service call that the upstairs central heater is not working. We find the sequencer is grounded out and keeping the heater from coming on. We replace the part and run test the heater. The central heater is working well just in time before the cold front comes in.
Service call that the Central Heater is not working. We find the variable speed blower motor grounded out. Replace the motor and run test the gas heater. The heating system is working properly
Service call that the heater is not working. Find the thermostat not wired properly to turn on the auxiliary heater. Run test the heater and everything is working properly. The family is back to being warm and comfortable.
Service call that the Heat pump is not working. Find the capacitor in the air handler for the blower motor burnt out. Replace the capacitor and run test the heater. The family is back to being comfortable and warm
Service call to check the Central Heater. Turn the gas valve on. No leaks at the gas valve. Start the gas heater up and check for carbon monoxide. The system is not leaking CO at this time. Since this is an older gas heater we advise the customer to get CO detectors.
Service call to check the Heat pump. The central air and heat system is working properly
Replace the Central Heater and Evaporator coils. Install new wood platform with a filter base to make changing the filter easier.
Service and check 3 central heat systems. Amp draw on motors are within specs. Coils are clean. The thermostat is calibrated. Heaters are ready for the winter
Service call that the thermostat for the Central heater is not working properly. Find the thermostat faulty and replace. Run test the central Heater and the unit is working well.
Central Heating service call that the heater is not working. Find the gas valve turned off and the return ductwork collapsed. turn the gas valve on and install new return ductwork.
Service call to service and start up the Central Heater. Everything is working properly on this Carrier gas heater in the attic