Professional, thorough and extremely knowledgeable.
Jeremy always does a great job and explains what needs to be done thoroughly.
Very well. Prompt, polite, patient. Spoke to both my daughter & me about options. I will definitely be calling you in the future
I got quick and insightful information as promised
He was great! Thank you, Jeremy
Jeremy deserves an A+ for coming out here right before thanksgiving and on his day off! He did a great job!!
fair on price and on time.......
Professional and courteous; no complaints.
Performed tune up maintenance contract. Turned system on from each thermostat and unit kicked right on. Started at indoor unit. Inspected unit for cleanliness and proper operation. Found blower wheel and blower cabinet have excessive debris. Inspected all electrical connections. Inspected blower motor and capacitor. Motor pulling 6 amps on stage 2 Filter is clean but filter grill is half off, Put back on Condensate is draining properly. Evidence of water backing up in condensate pan, Recommend dealing safety switch Have a 18 degree temperature split. Unit is operating at this time. Inspected condenser. Inspected unit for cleanliness and proper operation. Coils are impacted with debris from concrete construction. Inspected compressor, have a amp draw of 10 Condenser fan motor pulling .1 Contactor heavily pitted and sparking when contacts touch. Capacitor is 50 and measured 50 and is within spec. Suggest replacement of contactor, clean condenser, clean blower wheel, install ceiling
Out to estimate replacement of non opp 4 ton condenser for upstairs. After talking to client, found client would like estimate on 17 two stage air conditioner. Also wants estimates for downstairs system and to do both systems at same time. Gave estimate for upstairs only with 14 and 17 seer options and 14 and 17 seer options for both system.
Client stated unit was not cooling. Verified customers concerns. Found that the dual run capacitor was leaking and not operational. The blower capacitor was also heavily rusted and not up to spec. The curb on the unit was leaking air onto the roof. Replaced parts . Client went twitch club. Sealed curb
On arrival found the back toilet seal for the flushing mechanism was bad and deteriorating. Customer wanted to estimate to install customer supplied r/o system and to change to laundry bibs
Pair of PVC leak in backyard Customer had PVC leak in backyard inch and a half running into slab connect to a TV which feeds hose bib continues on 290 into a inch and 1/2 x 3â€œ bushing and then connects to 3 inch PVC this estimate is to cut out the bushing that is leaking connect three new PVC 90s and a section of pipe no greater than 2 feet
Spoke customers realtor Customer had home inspector Do a line inspection upon that inspection they found roots.We would have to camera line in order to give proper estimates for repairs or replacements.This estimate is the camera line locate Area in question and give estimates for repair. Must have homeowners approval in order to start work. Also clean out is below grade recommend raising clean out and putting a round clean out box with lid To prevent debris falling in sewer line
Upon arrival customer stated the gate valve wonâ€™t turn off all the way. Main water service enters through basement foundation And is galvanized and 90 degrees to a gate valve which is attached to copper on the other end.We will attempt to remove gate valve and cut the copper and install new ball valve and reattach to copper. Crystal blue is not responsible for existing galvanized. This estimate is to also include excavation of approximate 2â€™x2â€™x2â€™ hole to find pvc leak in back yard
This estimate is to remove existing PRV in brick we will have to go under house to cut waterline in order to remove PRV we will install new three-quarter inch PRV vertical so it is easy to access and not in the brick. We will install new hose bib and insulate pipes
Found drain line not draining cause of water leak coming from air supply Plenum. Found cause of drain line not draining is due to Double trap scenario. drain line sagging causing water to not drain appropriately airlocked. second trap filled with sediment due to this scenario. Flush drain line restriped drain line to have proper slope drain line now draining appropriately
Needs new PRV. Schedule appt for 7-28
Trane 2 ton package unit Trane 5 ton split downflow closet backyard. Will return after 10th of June to finalize the install and charge system. Electric company will be out on 10th to complete work then we can test system and charge with R410a Out for progress payment, 5000$ still waiting on pge. Client wants surge protectors added to system quoted 2 for 400$ Surge protector for 2 systems
Customer was concerned of odor coming from under house and wet spot in front of house check meter notice them moist or Tighten meter nut Crawled under home notice there was a leak coming from the Hvac system recommended having someone from our company come out to inspect Contacted our office they will reach out and schedule
Out to give estimate to replace through the wall heating and cooling unit. Client chose to move forward with $4000 estimate to replace Suburban unit with Suburban Dynaline 3. Lead time for unit is 5 weeks. Will order unit ASAP, and follow up with tracking. Collected $400 down payment.
Out to estimate replace of 2 furnaces and 1 package unit. Client in the buying process of the home. Sending estimates to real estate agent Kay Ismail.