Performed diagnostic in NewCastle. Furnace is blowing air but not cooling. Condenser has no power to unit. Disconnect is melted at top and wired incorrectly. Fuses in disconnect have been bypassed by someone else. Breaker panel Iâ€™m only getting 77.4 volts across the breaker itself. Then Iâ€™m only getting 25volts from one leg on breaker to ground. Breaker is bad and not sending correct power to disconnect. I recommend replacing the Breaker with a brand new one, replacing melted disconnect for outdoor unit, replacing out of range Dual capacitor, replacing bad hard start kit, and replacing contactor. All of this was damaged by a power surge to the unit. I Highly recommend to replace all electrical components in unit.