Found York condenser on side of house. Unit is relatively clean on inside and outside of unit. Removed weeds growing up near unit so they did not grow inside of unit. Checked all electrical connections and are okay. Checked capacitor and is in range showing 40.5/5.1 uf and is rated for 40/5 +-6% and is in range and okay. No signs of any damage to unit. Checked refrigerant pressures for R410a system and is showing Tested unit after maintenance to ensure proper operation. Used this visit as a.c tuneup part of membership.