The technicians were friendly, professional and courteous, Their work and follow up was outstanding.
Crystal Blue Plumbing provided excellent customer service. The technician (Chance) went above and beyond our expectations. After getting no help from our home warranty and given a high dollar estimate from a big name plumber, Chance assessed our problem and helped us get through the mfg. He found out that our problem was covered by a mfg recall and helped us get set up for repairs. In the end, we weren’t charged anything for the visit. I truly appreciate the honesty and excellent customer service we received. I would definitively use Crystal Blue Plumbing in the future and highly recommend them to anyone.
Sean came right out and knew the solution within minutes. Explained the situation and how to solve it then went right to work. Service call was quick , affordable , and professional. I've used Crystal Blue at 2 properties now and will always be a loyal customer because of their consistent performance. Thank you again!
Cable snake single drain line up to 50 feet Run water and flush to assist in stoppage debris flowing down and out of system Electronic video scan to confirm drain line clear
Repair will include soldering of condenser coil, pressure testing to verify no other leaks exist, will install a filter dryer vacuum system to below 500 Âµm and charge system to manufacture specifications. This repair will not guarantee system performance due to no refrigerant in system no guarantee compressor is in good shape cannot test. Due to system trying to run could have caused compressor damage from overheating with no refrigerant in system. During pressure test found service port valve stems leaking replace valve stems found no other leaks at this time. vacuumed system, charge system to manufacture specifications, turned on and tested unit operating running at this time Due to possible stress put on system running low or with no refrigerant no guarantee on how long system will run / operate
Performed annual a.c maintenance in West Sacramento. Unit is a Guardian Condenser on back side of house. Unit is overall in good condition. Checked all electrical connections and are okay and showing no signs of loose/damaged wires. Checked capacitor and is in range showing 74/5uf and is rated for 70/5+-6%. Condensing coils are dirty and will wash off to ensure higher efficiency of unit. Checked refrigerant levels for R410a and is showing 114 psi Lowside and 335psi Highside with ambient temperature at 95 degrees. Overall unit is in good condition with no red flags. Tested unit after maintenance to ensure proper operation.
Performed a whole home plumbing inspection, presented multiple issues to the customer and he chose the ones that are in the most need of getting fixed. Removed the broken kitchen strainer and installed a new one, filled the sink with water and let it drain with no leaks. Removed the stiff shower cartridge in the master bathroom shower and installed a new cartridge, turned the water on with no leaks and hot is left and right is cold. Cut the trap arm at the bar sink and ran the snake about 40 feet before i noticed the clog disappeared, ran water down the line for 10 minutes with no issues. Removed the black iron 90 degree elbow that was in the outside water heater closet, turned the water back on with no leaks.
swamp cooler diagnostic inspected tested swamp cooler found no issues or problems with swamp cooler. overflow drain not screwed on installed properly could possibly cause system to leak was not leaking at time of diagnostic due to the way the pipe was installed roof jack not being sealed could cause water to run down roof jack and into building this could cause the water issue the customer is having sealed roof jack. informed customer to run system and if problem occurs again will have to move stuff in warehouse and use scissor lift to get access to drain pipe attached swamp cooler may be leaking from there
Dummy Invoice to be able to move other invoice to correct project.
Completed install multiple things not finished unit not working due to tripped wet switch safety switch due to drain lines not connected properly sloped properly (installed properly) finished install in multiple other locations wrapping insulation around metal ductwork that was an insulated correcting flue pipe touching wood combustible material insulation on line set corrected and finished drilled hole in concrete and attached pvc Outside above new drilled hole through concrete.
Adjust swamp cooler belt to proper tension to relieve stress of motor and allow motor to run more efficiently without burning it out
Cleaned all condenser coilâ€™s and fresh air filters part of AC Quarterly maintenance. Found during condenser coil cleaning oil stain on condenser coil. That was not visible originally due to a dirty condenser coil. Found it to be caused from a screw somebody installed to install ground rods. possibly just finished rubbing through due to last service unit was working operating with no problems.
Here is another copy of the estimates. With warranty info. Trane is a 5 yr labor, 10 yr parts. Rheem we are doing 2 yr labor, 10 yr parts.
Out for estimate on replacement of 4 ton Ac system. Rheem 2 stage heat variable speed blower motor on the furnace 7 yrs old. Went over options for replacing the ac system with Rheem and or Trane. Looking for a 16 seer option. Zoned system with static bypass damper. Wireless Honeywell tstats wants nests tstats. Clients interested in new financing options. Will get Rheem equipment pricing and adjust quote then. Going to send it to them Monday and call mid day. To go over everything.
11 unit Qtrly Maintenance / HVAC systems, exhaust fan and make up air units. Performed AC maintenances #5 turned the unit on to check operation of system turned on / running with no problem. Checked refrigerant pressures good, checked amp draws compressor good, outdoor fan 1.0 good, capacitors 7.5 reads 7.6 within manufacturers tolerance +/-6%. Visual inspection of electrical - wiring good no burnt or overheated wire connections, Service disconnect good, contactor - contact points slightly pitting and burnt not affecting function / normal wear. Unit operating with no problems at this time. #4 turned the unit on to check operation of system turned on. Checked refrigerant pressures good, checked amp draws compressor good, outdoor fan 9.6 good, capacitors 7.5 reads 7.5 good. Visual inspection of electrical - wiring good no burnt or overheated wire connections, Service disconnect good, contactor - contact points slightly pitting and burnt not affecting function / normal wear. Unit opera
Customer has two floor drains that have a gas smell coming from them, two touchless faucets that are not working. One toilet has a broken wax ring and moves, another touchless urinal does not work and another touchless urinal that is leaking. Presented estimate to fix all the issues, they will contact us when they decide what they want to have fixed.
We will remove old equipment per EPA regulations and install a 4 Ton Trane 17 SEER/13 EER/80% two Stage Heat and Two Stage Cool with True Variable Speed Blower. We will install new flue pipe, new secondary drain pan, new stainless steel gas flex with gas sediment trap. Install wet switch. We will install new condenser pad with all new electrical disconnect and breakers. Perform nitrogen purge of line set and pull vacuum down to 500 microns to ensure no leaks of refrigerant. Charge system with R410a Refrigerant to manufactures instructions. We will install all new R-8 ductwork, to be strapped up according to code. We will install (1) new supply plenum and (1) Return plenum. We will install (7) supply ducts and (2) Returns. The second return is being added to the system to where the original setup only incorporated a single return. We will install a new Honeywell Zone Board with all new motors and mechanical dampers. Install (2) Nest thermostats. We will perform a Title 24 duct te