Called out for sewer clog. After speaking with the customer regarding the I recommended snaking the line. I was able to open the sewer line out to the septic tank. There was excessive amount of sludge that seemed to be the cause of the stoppage. I flushed the toilets and ran water to test. There is no signs of a back at this time. An estimate was left for the high pressure water jet to help remove the sludge.
Service call for slow tub drain.removed trip waste plate and cabled line.removed drain cover and pull debris out of drain.ran water to test drain and all appears to be working.recomended installing a new single ever shower valve.
Suction line wasnâ€™t properly insulated, leaked on spill switch and tripped the system, re-insulated, tested, system operational.
Started ac system, Che Jed pressures and temperatures. Installed surge protector on outdoor unit.
Ac tune up x2, checked all electrical components, cleaned evap coils with spray, out door coils were wiped down did not have a faucet near condensers. Took standing pressures could not get the compressors to start due to the cold weather. Pressures and all other components looked good. Changed the upstairs merv 11 filter, customer supplied the downstairs filter was still okay at this time n
Installed Amana heat pump system, new installed with 14 supply vents 2 small returns and central return In hallway, T6 Honeywell thermostat and 20x25 media filter. New lineset, pvc pipe for drain and emergency drain pan with float switch.
Flushed out hot water heater do to sulfur smell that bled through during a regeneration from previous visit. Tested for sulfur after flushing found non present. Also put softener in bypass as itâ€™s not softening water, found hard water present and possibly causing air in lines recommended to customer at some point water softener should be changed. Sulfur system is operating as should.
Called out for brown water in the water lines. After programming the softener and iron softener I set both for regen. I then drained the water heater and noticed a sulfur smell in the water. The customer recently changed from the first well pump to the second well pump and is noticing dirty water coming from the new well pump which is normal. An estimate was left for a water filter to filter out sediment coming into the house. And possibly installing a filter for the water heater.
Arrived at customer home for a clogged branch line. Cleared line.
Must return tomorrow to complete the job.
Called out for a leak on the second floor toilet. After opening a bigger hole in the ceiling there is a crack in the 3â€ copper drain under the toilet. I cut the wall exposing the stack line and will cut and remove the the pipe and fittings. We will remove the toilet and install a customer supplied toilet with new flange. The customer will call once they have the toilet they want to install. Cleaned up and collected a deposit for the job.
No hot water due to bad elements, recommend to have hot water replaced.
Found tripped breaker, reset, tested, system operational.
Called out for a leak on a drain line above the boiler. After assessing the leak I cut 2 sections of a 3â€dwv copper drain. After repairing the leak I then snaked the main sewer out to the septic tank. There is no signs of leaks or back ups at this time. Cleaned up and collected payment.
Completed annual maintenance on oil boiler. Found failed circulator pump. Replaced pump and checked operation. Boiler has had water damage for leaking pump drain above. Set appointment for plumber.