AC Repair & Furnace repair visit. investigated issues and Found unit gas valve to be off, gas pressures on low stage were set to 3.44. Also found AC fan speeds to not be set, set speeds for 2 tons of Air. Also found feel jumper for Y1/y2 To not be installed. All problems have been corrected.