Chris did a thorough inspection great at explaining everything he did
Jason was very professional as he went about doing our furnace maintenance check
Jacob was very professional
Did a thorough inspection and set my thermostat .
Tech left heating unit on high and wasn’t discovered until hours after visit.....
He took his time and did a thorough job with our maintence visit. He also explained all that he did.
Did a nice job tuning up our furnace. Thanks
Scheduling the appointment was a pain. I called the number but the person that answered wouldn't actually schedule an appointment. She took my name and number and had someone call me back. Called on Friday, didn't hear back until Monday. I was in a meeting so I missed the call. The voicemail told me to call the main number again, which started the process again. After finding a way to direct dial someone, I setup a service window from 3-5pm a few weeks out. On the day of, I hadn't heard anything by 5:30, so I called the main number. Mind you, I left work early to be home by 3. Again, the person couldn't tell me anything, she just took my information and was going to have someone call me back. Right after I hung up, I received a text that the tech was on his way. He arrived by 6, did his thing, and left about 6:45. He initially thought that the humidifier was inoperable but he hadn't turned it on from the thermostat. I helped him with this and then things were OK. Chalk that up to lack of experience on his part? Otherwise, Jacob was polite, tidy, cheerful, answered my questions/concerns, etc. He was all of those things you expect from service personnel.
Installed a new Amana 16 seer system.
We serviced a Amana Air Conditioner
We replaced a bad air conditioner fan motor on a York system
I serviced a 2003 Trane Air Conditioner, I checked electrical components and Freon pressures.
We installed a new Amana 13 seer air conditioner
Replacing blower wheel on older Armstrong furnace.
We diagnosed a bad Evaporator coil on a York system.
Recharge a 2010 York to proper freon operating pressures and test performance.
We worked on a 2011 Goodman Air Conditioner. We checked Freon pressures and electrical components.
Recharge 2010 York with freon and add leak sealant to prevent future loss. Tested for proper operation.
We serviced a 2011 Goodman Air Conditioner and we added R22 Freon.
We serviced a 2003 Lennox Air Conditioner.
We installed a two stage Amana Furnace with a modulating blower motor.
Replacing bad condenser fan motor in older carrier condensing unit.
Perform AC tune up on 1998. PM check on electrical, freon pressures, filter, air flow and performance of system. Check dampers and turn off humidifier. Clean AC. Replace blower cap to return system to proper operation.