30OCT2023 Jason Brown Arrived for new customer no heat, spoke with Michael about the systems performance. It’s never worked well, but now it doesn’t work at all. Inspected Airhandler. Found 120 to ground but only 10v instead of 240v. Inspected breaker panel. Found water draining down the panel, and the 60a 2 pole Eaton breaker corroded and split. Spoke with homeowner about my findings, he will contact a electrician. Left panel off, power off, and panel screws next to panel. System is not working at this time. I do not recommend restoring power to the home until an electrician has looked at it.