The service performed by Rod was great. AC unit found to be in good working order. I look forward to staying cool the rest of this summer.
Jake was very perfessional. He had a lot of patience and was not pushy
Arrived 30 and 31 July for a no cool found that evaporator was frozen due to a dirty air filters came back next day to check system after it defrosted found that the system was operating normally
Arrive 31 July for an air conditioning no cool Blue Shield found it had a bad compressor capacitor customer authorized replacement with the turbo system is functional this time have 12 A on the compressor and .9 A on the condenser fan motor charge is 20Â° of superheat and 16Â° of sub cooling.chris
Arrive 31 July for a condensate leak found condensate pump was bad customer authorized replacement of pump tested pop everything is flowing normally.Also noted that her unit does not have a float switch which could cause a leak in the evaporator recommended to the customer to install full switch.chris
Weâ€™re at 31 July for an air conditioning no cool found that the reset on the high limit switch on the condenser was tripped customer or already replaced contactor and capacitor on unit checked charge on unit system is running as it should at this time.
Right on 31st July for a return for repair previous text said the system was frozen up God check the charge found that the evaporator was extremely dirty clean the evaporator top system off for 2 pounds of 410 A also recommended to the customer that there could be noncondensibles in the refrigeration recommend estimate provided to the customer.chris
Arrived on 31st July to conduct an air conditioning preventative maintenance checked contactors capacitors and blower checked blower evaporator drain line checked charge on unit at 5Â° superheat was 7.5Â° of sub cooling system is working as it should change the filters.
Arrived for an air conditioning Newcomb checked capacitor on the blower she said there was no airflow she had the system off when arrived check the system it was extremely low on our 22 she authorized top off of 5 pounds she understands that she needs to replace the system because he has had a leak on it prior recommend replace.chris
I arrived for a recall on a blue club member. I inspected the system and found the system to be running at 4 deg subcooling which is where the subcooling was set at by us two services ago. I inspected the system and found that it calls for 12 deg subcooling per manufacture specifications on the systems data plate. I made the homeowner aware of this and I did not charge to a diagnostic fee to add more refrigerant to the system that we/I missed on previous services. We agreed to add what refrigerant was needed to get the system running. I added three pounds of R410A and set the systems subcooling to 16 degrees. And the range aloud is + / - 3 deg from 12 = 9 - 15. Once the systems subcooling was running properly I found the temperature difference across the evaporator coil to be 4.3 deg with a subcooling of 16. I let the system run for 30 minutes with correct subcooling levels per a TXV set up and the systems temperature difference from supply to return only gained 2 deg to 6.3 deg. And s
Came out for a no cool found a bad capacitor and hard start kit customer authorized replacement also found that while running the unit system went into want to do chemo because there is a heat pump tell the customer that the reversing valve is sticking was able to get it open back up system is running at this time but recommend replacing the reversing valve.
On July 30, 2021 I arrive to a previous customer nonmember upon arrival agree to the customer and then changed the UV bulb I wore no one gloves to make sure that no oil got on the boat self got it installed tested it showed the customer as well as took a picture Everythingâ€˜s working properly at this time thank you for your business Mike T
Condenser pad is sinking we will dig up around the pad slide bricks underneath to level it. 2 guys 3 hrs some bricks.
On July. 30th 2021 I arrive to a new customer nonmember upon arrival I greeted the customer they stated that the unit wasnâ€™t cooling check the thermostat and then walked around the building to find the exit to the roof got on the roof I checked the condensing unit it was running itâ€™s three-phase so no capacitor check the charge and the unit was pulling into a vacuum shut it down system only had 10 psi sitting on it give the customer option to get a quote for replacement since it was so low and the unit held 6.25 pounds of Freon customer declined wanted to put refrigerant in instead found a pinhole leak on the condensing unit were the tubes go through the metal plate itâ€™s a very small leak recommended replacement customer still denied said to go ahead and add the refrigerant I added 6 pounds of 20 to get 13Â° superheat unit has a piston in it everythingâ€˜s working like it should thereâ€™s no telling how long the refrigerant will last thank you for your business Mike T
30JUL2021 Jason B Arrived to new install having trouble keeping up. Spoke with Michelle about the systems performance. During the heat of the day the system is struggling to get down below 74 degrees. The hottest room is the master bed. Inspected coil furnace and condenser. Found the system running properly with ideal pressures and subcooling. Inspected ductwork in attic. Found system running on one 14â€ return. Making total intake cfm 450. This is a 3 ton system requiring 1200 cfm. I recommend increasing the duct run from behind the system to 18â€ hard pipe, then wying to two 16â€ returns. Increasing the existing return to 16â€ flex then cutting in a new return into the master hall or as close as possible. This should be a 14x30 return if at all possible to match their other. Cfm after increasing comes out to 1250 I also found the attic insulation to be lacking at 6â€ when recommended minimum is 13â€ at 1600 sqft I recommend blowing in 10 bags of insulation.
Arrive 30 July for a condensate leak found that the primary drain was clogged cleared drain customer authorized placement of pain treatment flush drain with Clearwater re-taped condensate line system is working as it should.
Came out to give estimate for installation of a mini split for a sun room. Due to there not being a viable access to an outside wall due to windows, I gave customer the option to do a mini split with a minor demo some brick and running the lineset through the chase and into the attic. Customer is limited on space and not many options available for heating and cooling. Told customer that I would get pricing of doing a PTech unit, but customer is on the fence about that option, due to the layout of the room they are wanting