12MAY2021 JB Arrived for spring tune up. Discussed system performance with Karen. Cycled system on at thermostat. Inspected blower motor, amps, coil, and cleanliness of furnace cabinets. Verified integrity of float switches. Found condenser coils to be clean and free from any vegetation or debris. Washed out condenser coils. Inspected electrical components. Hard start,capacitor, and contactor are functioning properly and in within specs. Fan and compressor amps well within manufacturers requirements. System is performing properly at this time.