We were so impressed with our technician & the service we received. He did an excellent job quickly, & kept us well-informed while he worked. He did a great job & we’ll definitely recommend your company!
Happy & professional!
Kianoosh took time to explain his findings and test results to me and explained what I could do to improve the performance of our HVAC systems.
Jake did a wonderful job!
I always love the service that I receive from Interstate.
Patrick was respectful, courteous, and efficient at his job. He wore covers on his shoes when he came into the house to ensure he didn’t make a mess. He was fast but also very thorough in his job and explained everything he saw. Would definitely use these guys again
Jason was simply wonderful. He was thorough and did great work while remaining friendly and informative. Would recommend him and Interstate to anyone looking for HVAC install or repair!
Replace blower motor in heater on a train system
Duct cleaning for ductwork in ceiling of home with a Lennox Heat and Air system.
AC maintenance on a 2013 Lennox system
Sa Trane system for summer. Replace filters. Add pan treatment. Clogged drain.
Perform a tuneup on the trane air conditioner. Wash the condenser coil, check all electrical components and R410a refrigerant pressures
Inspect 15 SEER Carrier Air Conditioning system with Silver Club maintenance plan.
Air balance analysis to determine why upstairs is not cooling as well as downstairs. Add hardpipe ductwork instead of flex duct for increased static pressure. Add whirlybird to attic to remove ambient attic heat load on ductwork upstairs.
Replace condensation pump to rheem air conditioner
Repair the Ruud air conditioner. Replace the dual run capacitor, add r22 refrigerant to dial charge in by superheat. Wash condenser coil
Carrier air conditioner summer tune up. Wash AC coil and change 10x20x1 filters
Repair the Lennox air conditioner. Add R410a to dial the charge in by sub cooling
American standard AC freezing up. Install low ambient fan cutoff kit
Install hardstart kit to bring down starting amps on carrier air conditioner
Air conditioning preventative maintenance on dual comfort maker systems for upstairs and downstairs.
Perform system evaluation of fedders air conditioner from 2005. Test refrigerant levels, capacitor and compressor amp draw. Found bad dual capacitor. Replace capacitor.