At first the tech said I needed to have freon added for $149. and also cost of a diagnosis call, $89.99. I told him I had already a diagnosis call and nothing was indicated as being needed and his office had said that there would be no charge for the diagnosis. I told him I would think on the freon. Brandon called back and said he went ahead and added nine oz. of freon and wouldn't charge for the diagnosis call. There was no charge for the service. That restored my faith in Interstate and the owners, Kai and Jamie.
Jordan did a great job
Arrived to call back performed system evaluation found system slightly low on r410a added 9 0z to system. Subcooling in range. System is cooling. Attic is very warm spoke to homeowner about insulation or whirlybird roof vents. System is cooling. No charges to customer at this time.
I came out for a no cool. I checked the system over and found the AC not coming on at all. Caused by a bad dual capacitor. With approval, I installed a new dual capacitor. I also washed the condenser coil. I cycled the ac and checked all operations. The house is 89Â° Inside. It can take up to 24hiurs for the system to fully catch up. All working at this time.
Silver ac maintenance asked about filters and how system cools, customer said system is cooling great. Customer asked about directional placement of filters, and showed customer that it is a downflow system, so the arrows should point downwards in the filter rack. Washed condenser thoroughly, checked dual capacitor. Capacitor reading out of range and with customer approval changed it up for a fresh one. Part is under warranty, but labor is not. Changed 10x20 customer supplied filters. Checked evap coil and blower wheel. Checked drain line and float switch. Checked amp draws inside and out. Checked refrigerant pressures via delta t. System is running well at this time, Amps on the fan side of the condenser are reading on the higher end of the manufacturer range.
I came out for a non-club AC maintenance. I washed the condenser coil. I checked the filter, blower, drain, evaporator coil, capacitors, contactor and all wiring. I cycled the AC from the thermostat and checked all temps, amps and charge. The filters were pretty dirty and need changed. I talked to the renter and owner about the filters. The owner said heâ€™d pick the, up and change them himself. All working at this time.
Preventative Maintenance Service on Goodman Residential AC System
Preformed fall maintenance on a 2013 Carrier furnace
Perform silver club furnace maintenance. Changed filters, check capacitor and motor amp draw
Duct cleaning home with 2009 Payne heating and air conditioning system and galvanized hard pipe ductwork.
Full system change out with carrier equipment.
Bryant AC not cooling. Found clogged drain line. Blow out drain line and install pan treatment
Repair the carrier air conditioner. Wash the condenser coil. Add R410a refrigerant
AC repair, found leak in evaporator coil
AC Tune Up on Carrier AC System
Trane and American standard AC tune up
Perform an air conditioning tune up