FOUND BREAKER IN MAIN PANEL TRIPPED DUE TO WIRE WITHIN DISCONNECT SLIGHTLY RUBBED THROUGH CAUSING SHORT. REPAIRED WIRING SYSTEM UP AND HEATING.
REPLACED FAULTY 60A SQUARE D BREAKER IN DISCONNECT FOR HEAT STRIPS. SYSTEM UP AND HEATING PROPERLY. INVESTED IN PSA (1) SYSTEM. SCHEDULE 1ST VISIT.
919-853-2539 EXTRA CONTACT. FOUND WASHABLE METAL RETURN FILTER INSTALLED INCORRECTLY CAUSING NOISE UPON BLOWER STARTING. RE-POSITIONED FILTER. CYCLED SYSTEM WITH NO CHALLENGES. INVESTED IN ESA (1) SYSTEM. SCHEDULE 1ST VISIT.
Tech washed and serviced unit and found no challenges at this time customer decided to switch to mpa customer paid 26 for first month via card. Card is saved on file for monthly drafts
Consultation Code: ENGEJ9W05
Tech found compressor not running due to yellow wire being left unplugged from dual run capacitor after tune up. Tech plugged yellow wire back onto capacitor and tested system. Back cooling correctly. Service warranty/no charge.
Upon arrival homeowner stated she wanted ground register moved to wall tech spoke with office and they stated we wouldn’t be able to due to a Joyce being in the way recommended getting low profile vent register spoke to homeowner about it. Tech preformed PTU today tech found no challenges at todays visit system is operating correctly at this time. Wife was home but husband is in rehab should be back in a couple days but tech spoke with wife about plans tech explained benefits and pros of being on the esa but she stated that she would wait for husband to make a decision. Tech collected 159.06 for ptu via check. Wants invoice mailed.
Tech washed and serviced unit
Tech arrived and found window unit was problem, informed customer to call small appliance repair.
Upon arrival customer stated he has smelled a natural gas like smell near the return downstairs. Tech could smell the gas as well. Upon inspection tech found gas leak beside gas valve in gas line at unit. Tech tightened all fittings on gas line and tested for leaks. No more leaks at this time. Tech found no further challenges, both systems are operating properly.
DAVID C AND DEMARQUS REPLACED THE UPSTAIRS TRANE SPLIT HEAT PUMP
Performed tune up on American standard gas pack.
Tech is servicing a Trane dual fuel system.