HOT TUB LINE- 1) Run 60 amp/6-3 Romex circuit from panel to other side of home and sleeve with 1 1/4inch pvc conduit down side of home into pvc junction box. (Approximately 30ft) 2) Dig trench from junction box to desired location of hot tub disconnect. Disconnect must not be closer than within 5ft of hot tub and not fuurther than 10ft. (Approximately 40ft trench) 3) Install approximately 40 ft of 1 1/4 inch pvc conduit in trench and pull 3 #6 gauge and 1 #10 gauge wires through out conduit. 4) Install mounting bracket and 60 amp GFI SPA disconnect at hot tub. 5) Run pvc conduit from disconnect to hot tub and terminate circuit into SPA motor. UPDATE ALL OUTDOOR OUTLETS- 1) Remove 10 outdoor outlets and old weather proof covers. 2) Install new weather resistant GFIs and receptacles with in use weather proof bubble covers.