It was a horrible experience to me . I was charged $ 4000.00 to change the panels and wirings “inside and out “ but not all of those were done. The dryer stopped working . I called the office , they scheduled the technician to go back to the house . I waited for more than 1 hour for him that afternoon ,but he did not show up. I found out later that he came early . Well after that, my dryer still would not start . The following day I called the office of my concerns and spoke to Lauren , she was not sympathetic at all , she screamed at me and hung up the phone on me , I felt so bad. I was afraid to call after that . Later I was sent a signed acknowledgment letter in the email saying that I was fully satisfied of the work done . Well I was not satisfied And I am still not satisfied and also I did not sign it , my tenant said she did not sign it . I know that my tenant has a visitor in the house that does not speak English . I do not think it is right for them to let the visitor sign a paper that can’t understand what they are signing . The owner was supposed to sign not the tenant or the visitor . In my conversation with the Technician he thought that the dryer got burned out . Few days later , I had repairmen come out to repair the dryer but those 2 people could not make it start either . I eventually bought a brand new one and that would not start either . I plan to call Kings Electric again but I am afraid . I am also still waiting for the copy of the paper /forms that i signed that they were supposed to email to me . I still have not received those . I also do not have a paper that shows I have a 3 year warranty as promised to me by the Technician. To me it was a horrible experience .
Nick did every well, he walked me through the process
Excellent service and very professional
Was here 5 minuets and collected $90.00
Great service from Nick
As expected, The technician was on time, courteous and finished the job in a timely manner.
Job # SHMPA29FD4DC-1 PHM 0936570
Dear customer. Weâ€™re happy to give you the estimate to â€” Charge R22 refrigerant up to 4 lbs â€” Recommend replace the systems as soon as you can to prevent the shortage in the equipments, your AC systems are at the end of their life, 16 years old Thank you for choosing us and feel free to reach out for more details **********Jason - Kings Electric & AC**********
Remove old ring flood and install new ring flood light over the garage.
Supply and install compressor
Gave estimate over the phone to replace
Low Freon, I added 2 lbs of Freon. Leak check at the copper joints we soldered but there are sealed, told customer if it low on Freon again, it has the leak somewhere and leak detection needs to be performed
Permit Fee Drawings / Inspections / Tighten screw for Neutral.
Happy Monday Miss McGee. Today we had the pleasure of Installing a bonding bushing to your metal service conduit to properly ground your service run. We then ran a new strand of 2/0 wire to replace the line that was trimmed and deemed an electrical hazard by the city inspector . As a result we are now ready to pull the permit and resolve the issue with FPL and the City of Miramar. It was a pleasure helping you with your electrical needs and we look forward to helping you out again in the near future.
SHMP2244BB91-1 PHM 0748207 1) Furnish and install new 45A breaker for Air Condensers Disconnect 2) Install new Fuesed/Breaker Disconnect for Air Condenser 3) Provide 220 whip to condenser unit
SHMP2244BB62-2 PHM 0748206 1)Replace and install New 150A Outdoor Main Disconnect Panel **Panel Needs Changing due to elemental damage. Bus bar has corrosion and breakers no longer make proper contact raising the hazard for arcs.** 2)Furnish and install new 45A breaker for Air Condensers Disconnect 3)Install new Fuesed/Breaker Disconnect for Air Condenser 4)Provide 220 whip to condenser unit
Diagnosis and repair outlets not working in living room, bedroom and bathroom Replace (3) outlets
Install installation on copper lines
Performed PM R.C.S. Upon arrival noticed float switch not working and A/H Drain Pan full on algae/gunk. Clean a/h pan thoroughly and VACCUM line . Also lay drain tablets and spray drain treatment . On C/U voltage regulated and Run cap going bad rated for 45/5 tested at 38.19. Fan motor tested as overamping and run cap will need to be replaced soon. Cut in new filter for customer. New Delta t is now 15 degree subcool . Will recommend safety float switch, Run cap 45/5 and outdoor fan motor