It was a horrible experience to me . I was charged $ 4000.00 to change the panels and wirings “inside and out “ but not all of those were done. The dryer stopped working . I called the office , they scheduled the technician to go back to the house . I waited for more than 1 hour for him that afternoon ,but he did not show up. I found out later that he came early . Well after that, my dryer still would not start . The following day I called the office of my concerns and spoke to Lauren , she was not sympathetic at all , she screamed at me and hung up the phone on me , I felt so bad. I was afraid to call after that . Later I was sent a signed acknowledgment letter in the email saying that I was fully satisfied of the work done . Well I was not satisfied And I am still not satisfied and also I did not sign it , my tenant said she did not sign it . I know that my tenant has a visitor in the house that does not speak English . I do not think it is right for them to let the visitor sign a paper that can’t understand what they are signing . The owner was supposed to sign not the tenant or the visitor . In my conversation with the Technician he thought that the dryer got burned out . Few days later , I had repairmen come out to repair the dryer but those 2 people could not make it start either . I eventually bought a brand new one and that would not start either . I plan to call Kings Electric again but I am afraid . I am also still waiting for the copy of the paper /forms that i signed that they were supposed to email to me . I still have not received those . I also do not have a paper that shows I have a 3 year warranty as promised to me by the Technician. To me it was a horrible experience .
Nick did every well, he walked me through the process
Excellent service and very professional
Was here 5 minuets and collected $90.00
Great service from Nick
As expected, The technician was on time, courteous and finished the job in a timely manner.
Low Freon, I added 2 lbs of Freon. Leak check at the copper joints we soldered but there are sealed, told customer if it low on Freon again, it has the leak somewhere and leak detection needs to be performed
Permit Fee Drawings / Inspections / Tighten screw for Neutral.
Happy Monday Miss McGee. Today we had the pleasure of Installing a bonding bushing to your metal service conduit to properly ground your service run. We then ran a new strand of 2/0 wire to replace the line that was trimmed and deemed an electrical hazard by the city inspector . As a result we are now ready to pull the permit and resolve the issue with FPL and the City of Miramar. It was a pleasure helping you with your electrical needs and we look forward to helping you out again in the near future.
SHMP2244BB91-1 PHM 0748207 1) Furnish and install new 45A breaker for Air Condensers Disconnect 2) Install new Fuesed/Breaker Disconnect for Air Condenser 3) Provide 220 whip to condenser unit
SHMP2244BB62-2 PHM 0748206 1)Replace and install New 150A Outdoor Main Disconnect Panel **Panel Needs Changing due to elemental damage. Bus bar has corrosion and breakers no longer make proper contact raising the hazard for arcs.** 2)Furnish and install new 45A breaker for Air Condensers Disconnect 3)Install new Fuesed/Breaker Disconnect for Air Condenser 4)Provide 220 whip to condenser unit
Diagnosis and repair outlets not working in living room, bedroom and bathroom Replace (3) outlets
Install installation on copper lines
Performed PM R.C.S. Upon arrival noticed float switch not working and A/H Drain Pan full on algae/gunk. Clean a/h pan thoroughly and VACCUM line . Also lay drain tablets and spray drain treatment . On C/U voltage regulated and Run cap going bad rated for 45/5 tested at 38.19. Fan motor tested as overamping and run cap will need to be replaced soon. Cut in new filter for customer. New Delta t is now 15 degree subcool . Will recommend safety float switch, Run cap 45/5 and outdoor fan motor
Add switch to existing box
Dear customer Weâ€™re happy to give you the estimate to repair the pool light circuit that has been broken when removing tree stump During the short diagnosis, we found out that the pool light transformer was short as well. We recommend replace the pool light transformer and run new conduit â€” Supply and Install (1) 300W 12v pool light transformer â€” Remove and discard existing conduit â€” Run new conduit underground and connect to new transformer. Approximately 30ft Thank you for choosing us and feel free to reach out for more details
Hey Nelson! Thank you for choosing Kings Electric & A/C for your electrical upgrades. Today I was able to finish the job of replacing your existing main breaker panel, with a new one that has space for outside circuits and I added a surge protector as well, everything was tested and is working correctly once again. If you have any questions or concerns, please reach out. Your Electrical Technician, Xavier
Hey Walter! Thank you for calling Kings Electric & A/C for your electrical upgrades. Today I was called out because youâ€™ll like to upgrade your service from 150 amp to 200amps. I explained to your wife about the job and what it consists of, if you have any questions or concerns, please reach out. Your Electrical Technician, Xavier
Today we went back to the job because the dryer issue is still occurring. Did extensive troubleshooting with Phil on the phone and the outlet is reading the 240v but dryer will still not turn on. Told customer to get new dryer cord to see if that is the issue, if not to call us back and talk to Phil.