Tech was very professional
Pickerington Heating and Cooling employees are all very professional. I have been a customer for many years and have never had a bad experience. Thank you
When a problem arises with my HVAC, I think of no other firm.
Quick,knowledgeable,courteous,dedicated and professional...just a few words to describe the recent experience with Mike from Pickerington heating and cooling!The office staff were quick to respond when I called and always called back when they said they would.All this during the recent "cold spell"when temps were below zero!
The technicians are always friendly and knowledgeable.
The technician was friendly and knowledgeable.
Whole House Duct Cleaning for a 2,400 sq ft house.
Furnace Tune Up & Safety Inspection on Comfortmaker Air Handler
2009 Carrier Heating and Cooling System found leaking water due to a clog. Unclogged the system and repaired the trap kit and installed an overflow pipe. System is no longer leaking water.
Upon arrival customer stated that the TRANE unit was not turning on, tech found no voltage coming through circuit board, found the low voltage wires that supply power from the transformer to the circuit board were loose, tech re-secured wires, cycled, system is now running, delta t is 75-55 (20 degree drop) system is cooling, OUTDOOR UNIT HAS 245/245 LINE VOLTAGE, 26.2 LOW VOLTAGE, FAN AMP IS 1.1/1.4, COMPRESSOR AMPS 10/18.
Performed a diagnostic on a Trane AC. After inspecting, the 240 volt wires were burnt and caused a short. Replaced the wire and confirmed unit is working now.
Tested Freon levels on RHEEM unit. Filled at customer request. Customer requested estimate on new unit.
Arrived and Found house at 68 degrees. Checked pressures/ coils. Removed outside debris and customer opted to clean themselves.
During diagnostic visit, Found pressures at 40/180 checked delta t at 14 added freon at customer request new pressures at 70/200 with a SH of 28 unit is operating as expected at this time
During A/C vist, found 50/5 capacitor had exploded, replaced at customer request.