Performed preventive maintenance on Lennox AC system.
Performed preventive maintenance on (2) Trane AC Systems.
Diagnosing Aprilaire 760 humidifier.
Making repairs to an improperly installed Goodman furnace.
Performed Fall preventive maintenance on Trane Heat Pump system.
Cleaning burners of carrier furnace on a maintenance inspection.
Performed preventive maintenance on Gas Furnace
Installing 75 gallon natural gas water heater.
Performing maintenance inspection on Trane XL16I. Also replacing capacitor and cleaning coils.
Performed diagnostics and repairs on Carrier Heat Pump system
Performing maintenance inspection on 2 Trane XL16I units. Found a snake and mouse nest in one from the winter.
Performed preventive maintenance on AC system.
Performed start up on new Rheem AC system we installed.
Performed diagnostics and repair on Trane Evaporator Coil drain.
Performing maintenance inspection on 2 Trane AC units.