Great service, very professional, Flexible Scheduling.
The tech was very polite and knowledgeable..
Found rheem gas furnace not heating correctly
American standard gas furnace near Dover Ohio 44622 not heating found fresh air pipe not connected properly and weak flame sensor on this gas heater
Repaired a carrier gas furnace in Dover Ohio 44622 near new Philadelphia Ohio replaced the control board due to the igniter was not coming on. Heater is now working and heating the home
Refilled ac with r22 Freon in Dover Ohio 44622
Repaired a gas furnace near new Philadelphia Ohio. Has a defective plenum limit on a Concord gas heater. Replaced the limit on the natural gas furnace and replaced the filter. System is running at this time but the return air drop which was put on by another hvac company is incorrect. Per installation of the natural gas furnace return drop can only be hooked up on the sides or bottom. Recommended customer reach out to the other hvac heating and cooling company .