The technician docs great job.
I called for a furnace repair and they responded to my home in less than 20 minutes, great service , just moved here and I will continue to call Hey Neighbor if service is ever needed again. Thank you !
very prompt , fast and great job
Love the fact it was same day service
Great service definitely a blessing. Ron was very courteous and very professional and I definitely appreciate his service .
Dave was very friendly and professional and did a good job.
Great service call all ok!!
Furnace repair near Louisville Ohio 44641. Found the furnace has a defective blower motor not allowing the unit to blow heat through the home. Replaced the belt drive blower motor and adjusted the fan belt now furnace is properly heating the home
Replaced inducer motor
Found airease furnace near Louisville Ohio 44641 not heating up the home correctly. Found the variable speed motor is working good at this time. Found the gas furnace has a weak flame sensor reading going back to the control board which was causing the furnace to shut down the burners prematurely. Replaced the flame sensor on this natural gas furnace and now we are heating up the home as needed.
Fixed York gas furnace in Louisville Ohio 44641
Found Trane gas furnace not heating up correctly. Found filter plugged up and bad flame sensor. Replaced flame sensor with a new Trane part now the heater is working correctly at this time.
Furnace service on a natural gas furnace in Atwater Ohio
Repaired door switch
Furnace tune up
Removed a 3 day old puppy from a return air duct he feel into.
2 furnace repairs