Fixed issues really quickly
Very nice guy. Worked quickly. Repair done.
5 stars very effecient friendly n on time actually early better then cable lol very satisfied b blessed b safe thank u
Everything went well, he was very efficient and had the problem fixed pretty quickly
Very helpful & nice
It took three days to figure out the problem and resolve the issue and the initial contact took a day and a half to happen but once the repairman did arrive he was courteous and did his best to resolve the problem which took two attempts to resolve.
Excellent job, covered all the bases. Completely satisfied, will be calling again.
Ron did an excellent job in fixing my furnace and explaining what needed to be done.
Repaired condenser in Warren Ohio
Carrier air conditioner repair in Warren Ohio 44485
Found air conditioner in Warren Ohio not cooling. Replaced capacitor and added refrigerant
Lennox gas heating service in Warren Ohio 44484
Reaping a Lennox gas furnace near warren Ohio 44484
Serviced concord gas horizontally furnace in the attic near warren Ohio. Cleaned the flame sensor
No cried gas furnace not heating home found defective pressure switch. Replaced and system working good
Found a natural gas furnace not allowing the ignitor to come on. Found unit has a defective pressure switch
Replaced flame sensor
Lennox gas furnace not heating home correctly near warren Ohio
blower making noise
Found gas furnace near Warren Ohio 44483 had been tripping on limit switch. Replaced plenum limit on heating system and all is working good at this time
Hey neighbor heating and air conditioning of Warren Ohio was called for a furnace not heating the home. Found the igniter was bad. Replaced igniter and now the gas furnace is working
Found fan belt needed needed to be replaced natural gas furnace near Warren Ohio
Found nest thermostat not turning the furnace on and off correctly. Replaced thermostat with a new stat and heating system is working correctly at this time furnace needs to be cleaned