Showed up in tit manner. Polite , and hot my furnace running.
I would have him back again
Ron always does a great job
Ron is friendly and knowledgeable
Ron was nice. Would recommend hey neighbor to everyone
Him and the work was very good thank you and him for the heat
Awesome. Great job, fast and perfect.
Found dia one gas furnace short cycling and not keeping house to desired temperature. Found flame sensor bad replaced with oem part and system is now heating up and keeping up with tempature
Furnace repair near boardman Ohio 44512
Found luxair furnace near Youngstown Ohio 44505 not heating up the home after inspection of the Hvac unit found the igniter was bad replaced with new igniter now system is working properly
Hey neighbor local time Youngstown Ohio 44512 near boardman Ohio found the blower motor had filter in it causing it to vibrate
Found luxaire gas forced air furnace near Youngstown Ohio 44509 no staying lite. Found the flame sensor was bad replaced with a new luxaire oem flame sensor and heater is working at this time
Heating system needs repaired called hey neighbor for service and had our furnace repaired that same day.
Furnace repair near boardman Ohio 44512. Found system working fan running fixed g terminal
Found rheem gas heating unit had a dirty filter which caused unit to prematurely tripp the plenum limit on the furnace. Reset the limit and removed the clogged filter then cycled the gas furnace on and off several time to make sure the heating system was correctly working. System in good working order at this time recommended to the home owner he change his filters every 30 days.
Changed defective flame sensor
No heat needed repair service near Youngstown Ohio 44505
Found no heat near boardman Ohio on an amana natural gas furnace. Found defective pressure switch and now heating system is working good
Hey neighbor in Canfield Ohio repaired the Hvac unit
Found luxaire natural gas furnace not working on arrival. Found the heating unit had a defective flame sensor. Removed and replaced the heating systems flame sensor and now the furnace is heating the home.
Repair heater in Youngstown Ohio 44507. Gas furnace blower not working repaired with a new blower motor capacitor