I received excellent service in a short amount of time.
Very professional.would call again
My husband said he was very polite went to check the problem, fixed him promptly and said have a nice day! I appreciate great customer service thank you
Excellent no problems
Very good honest
Ron came in, new exactly what was wrong and how to fix it. Was here for a short amount of time and my furnace was running great. Still is.
Kalvinator gas furnace repair. Replaced primary limit. Thanks for choosing hey neighbor of Youngstown Ohio
Found gas furnace not heating up. Flame sensor is sending weak reading back to control board. Replaced flame sensor and furnace is heating up correctly at this time. Thanks for calling hey neighbor heating and cooling in Youngstown Ohio
Adjusted fan motor to help fan belt from slipping on pully. System is working correctly at this time heating the home
Replaced part on carrier gas furnace in Akron Ohio
Found dirty filter in goodman gas furnace clogged up not allowing furnace to move enough air
Rheem gas furnace repair near Poland Ohio 44514. Found furnace has a defective inducer motor. Replaced the combustion motor with new oem part. System working at this time thank you for using hey neighbor heating and cooling
Furnace repair in Youngstown Ohio 44502. Found natural gas furnace has no flame found defective hsi on unit replaced and now heating home correctly
Trane gas furnace ignitor not coming on. Replaced hsi and system working correctly at this location in Younvstown Ohio 44502
Whirlpool gas furnace repair near Younvstown Ohio 44505. Found unit kicks on and runs for about 3 to 4 minutes then shuts down. Found plenum limit prematurely opening up and turning the gas off in the furnace. Replaced the part and cycled the heater several times all appears to be working correctly at this time. Thank you and feel free to call hey neighbor heating and cooling for any future furnace repairs www call heyneighbor.com
Furnace not igniting properly. Adjusted hsi and now firing correctly
Furnace repair near Youngstown Ohio 44502. Replaced hot surface ignitor
Water leak from furnace. Found backed up drain will return to work on Trane heater location in Youngstown Ohio 44505
Furnace repair near Youngstown Ohio 44511 on an goodman natural gas furnace.
Gas furnace no heat near Youngstown Ohio 44505. Found rheem gas furnace limit tripped from dirty filter. Removed the air filter from the return air drop in the furnace and now have good air flow. Thank you for your business hey neighbor heating and air conditioning
Found a defective luxaire flame sensor near Youngstown Ohio 44504