My husband said he was very polite went to check the problem, fixed him promptly and said have a nice day! I appreciate great customer service thank you
Excellent no problems
Very good honest
Ron came in, new exactly what was wrong and how to fix it. Was here for a short amount of time and my furnace was running great. Still is.
The service tech was very friendly and explained everything.
Repaired gas furnace near Struthers Ohio 44514
Furnace repair in Youngstown Ohio
Air conditioner near Youngstown Ohio 44504 not cooling leaking water all over the basement floor. Unit was low on refrigerant
Found Bryant air conditioner not cooling the home correctly. Found the outside condenser motor running but the compressor was not running. Checked the ac unit found it has a defective capacitor. Replaced capacitor and the compressor started up and system is cooling at this time
Air conditioning repair near Younvstown Ohio 44515. Replaced condenser fan motor on an American standard r22 air unit.
Goodman gas furnace not coming on found breaker tripped reset breaker and tightened connection in furnace now system is working
Air conditioner inspection of a Trane unit we installed last year
Found natural gas furnace near Youngstown Ohio 44506 not keeping home cool and making noise per home owner
Furnace blower motor repair near Youngstown Ohio 44506. Replaced capacitor
Air conditioning maintenance done for the year on a carrier Putin air conditioner
Carrier gas furnace near Youngstown Ohio 44502. Replaced flame sensor needs new filter
Found gas furnace needs a flame sensor and fiilter
Diva one gas heating system near Youngstown Ohio 44512. ( boardman ). Found has a defective flame sensor replaced now furnace is heating home correctly
Found a luxaire gas furnace near Youngstown Ohio 44515 not igniting burners. Found defective hot surface igniter replaced with new factory oem part and system is heating home correctly at this time
Found a inducer motor on a weather king furnace manufacturer from Rheem HVAC. Replaced the motor with a new oem motor and now the furnace is heating the home correctly.