Performed tuneup on Trane furnace
Performed tuneup on Rheem furnace.
Performed tuneup on American Standard furnace.
Performed a service call for a basement unit making a humming noise and the thermostat fan was switched to on instead of auto to fix the noise.
Replaced the TXV and added 8 pounds of 410A refrigerant under warranty on a Saturday.
Performed a service call for a unit with no cool. Found that the unit was out of 410A refrigerant and performed a leak search. Found the leak in the evaporator coil.
Performed an AC tune-up on a Carrier
Installed a 3 ton 14 Seer American Standard full system for the main level and installed a new drain pan, float switch, and new in line switch.
Performed a tune-up per the service agreement and found the condenser motor to be going bad and over heating. Gave a recommendation to replace with system with a 2.5 ton Rheem 14 Seer.
Completed an estimate to replace the garage unit with a 2 ton 14 seer American Standard unit.
A service call was performed on a unit with no cool and 1 pound of 410A refrigerant was added to the system
Installed 4 Ton 14 Seer American Standard package unit
Performed Furnace tune up on an Amana system.
Performed Furnace tune up on a Lennox system.
Performed Furnace tune up on an American Standard and Trane system.