Service was good and the technician was very pleasant.
The technician was very polite and professional. The 3 hr wait time can be a little too much, but understand it.
Tune up on gas furnace, changed filter 14×25×1,vacuumed burner and blower compartment, tested for carbon monoxide, no carbon monoxide detected, system is heating properly, but should be replaced based on age..furnace is 22 years old
Performed an AC tune-up on an American Standard
Performed a service call for a customer with no cool on a single system. Replaced the 35/5 capacitor and used a hose to cool down the compressor.
Installed a 2 ton 14 Seer American Standard condensing unit and coil with a new pad and p trap.
Gave an estimate to install an American Standard A/C and E/C 2 ton system with a crane.
Performed a service call for a unit making a loud noise and lowered the blower speed.
Performed an AC tune-up for a service agreement customer on a Goodman and added cleaner to the drain.
Performed an AC tune-up on a Carrier for a service agreement commercial customer.
Installed a 12K BTU mini split for the foyer in the elevator room
Replaced the low voltage wire from the A/C to the furnace for a service agreement customer
Installed a 2 ton Seer American Standard full system for a senior discount. Added a new float switch, drain pan, and in line switch. Removed the old unit and put the new one on the roof and installed a nest thermostat.
Performed an estimate to replace the system
Installed a 2 ton 14 seer American Standard full system for the main level and installed a nest thermostat
A tune-up per the service agreement was completed on a Rheem and the drain was cleared.
Found bad capacitor on Amana straight's cool contenting it replaced now cooling