Left everything perfect.
Todd was courteous and efficient.
Excellent service as usual
Send reminder emails to customers, during spring and fall tune ups.
Adjusted door for water heater room
Replaced 45:5 run cap on a Lennox unit unit is running 2 specs
Fixed flue pipe from furnace and water heater on an American standard furnace
Gave estimate on a to head ductless Mini split American standard For basement
Provided estimates on Carrier infinity air conditioning system 2 stage variable speed infinity contorl system
Diagnosed and found blown contact or and overload relay on train 25 t commercial straight cool air handler
One system tune-up on an American Standard air conditioning
Working on a first company vertipak 1 and 1/2 ton for a commercial application
Two system air conditioner tune-up onto American standard systems. Recently installed.
Single system air conditioner tune-up on a Trane 5 ton R-22 system. Compressor pulling high amps, washed unit and amperage dropped. Unit is 13 years old and in fair health.
Two system air conditioning tune-up on two American standard 2 ton systems. Changed both 16 by 25 by 1 filters
Replaced blower cap and thermostat on a Trane system
Service agreement tune-up in Amana furnace
Service agreement tune-up on a Trane system