Heber took his time and explained everything to me and it really made a difference!
A Team is always very reliable. They show up when they tell you and answer any questions I have.
Todd did my Fall Tune-up and he noted that everything is working perfectly. The filter was still clean, so did not need replacing. He also checked CO2 level and got a zero reading, so no problem.
Angelo was prompt, efficient, informative, experienced,
Tune up Rheem systems and American standard systems with ultravasion filter systems
2 tune ups on Lennox 90 % furnaces with Honeywell media filtration
Installed 2 ton full systems drain w/float switch
INSTALLED 2 TON FULL SYSTEM
Performed heating system maintenance
INSTALLED 50 GALLON HOT WATER HEATER
INSTALLED 2 TON AMERICAN STANDARD 16 SEER VALUE SERIES
Performed tune up on heating system
Furnace shutting down due to no blower operating the unit. Board not putting line voltage to blower. Replaced circuit board.
Performed tune up on heating system.
No heat from furnace. Draft inducer was clogged. Took apart and cleaned the pressure switch. Now heating correctly.
Installed 2 ton Rheem furnace and hot water heater.
Installed 16 seer Rheem furnace.
2 service agreement fall tune ups on rheem furnace and carrier furnaces
2 system tune ups on American standard variable speed furnaces