Mike did a thorough job to correct the issue. But the problem was created by the previous Technician who can three days prior for standard maintenance check. He disconnected the wire to the motor/fan and didn’t reconnect it, causing the furnace to overheat and cut itself off with built in safety mechanism.
Always great service. Always services my unit quickly, especially when I've had problems. Appreciate getting the heat working when it's gone out during a cold spell or fixing the AC during Summer heat. I like that the same technician is always sent to my house. Great service.
Performed an AC tune-up for a service agreement customer on 2 Lennox systems.
Acid washed 3 condenser coils, repaired low voltage wiring for unit #1, and insulated the suction line for the gym unit for a service agreement commercial customer.
Performed a service agreement AC tune-up on 2 Rheem systems
Performed an AC tune-up on 2 ICP systems. Repaired a clogged drain line on the main level system and replaced the 35/5 capacitor on the upstairs system.
Performed an AC tune-up on an American Standard
Performed an AC tune-up on 2 Trane systems
Installed a 3 ton Lennox used condensing unit and added 3 pounds of 410A refrigerant
Performed an AC tune-up on 2 American Standard systems and a Carrier system. Added cleaner to the pump on all the systems for a service agreement customer.
Performed a service call for a customer with no cool. Replaced the 50+5 capacitor to repair the system.
Performed a service call on a Sunday for a service agreement customer with water in the the pan in the attic. Added a union, blew out the drain line, and replaced the pan float with an in line float.
Performed an AC tune-up on 2 Lennox systems for the sale of the home
Performed an AC tune-up on a Rheem and a Goodman. Blew out the clogged drain tube on the Goodman.
Installed a new 2 ton Rheem 14 Seer condensing unit and matching coil in the attic.
Installed a new return 10" with a boot and collars with a grill for the bonus room,.
Performed an AC tune-up on a Rheem and replaced the ultra filter.