Performed a service call for a single system with no cool. Replaced the 40/5 capacitor and washed down the condenser coil to repair the system.
Performed furnace tune up on two American Standard systems.
Performed furnace tune up on a Goodman and Rheem system.
2 heat tune ups on american standard furnaces. Propane conversion kits installed. New water heater. Changed both filters.
Ac tune ups on 2 American Standard systems
Performed heating system maintenance on customers 2 systems. Replaced the condenser fan motor on the upstairs unit.