Jason DeWeese was excellent.
Russ didn’t come to my house this time, Jason did.
2nd time meeting with Justin and received excellent service ad usual. Always had to follow up on Daweese’s jobs!
Joel is efficient and professional
Great tech. Want him every time!
Arrived on time, checked the system out, changed the filter and washed the outside unit
Joel Sisk was very helpful!
good job, good people. And no-one tried to sell me anything
1 system checkup on upflow gas unit. Flame sensor cleaned, filter changed, blowers checked. Found the capacitor to be low which customer was aware of. Temp rise within range. Only recommendations are to replace the 3 way grills and upgrade the thermostat to one that isn't a mercury bulb.
Both systems checked and are older systems. Flame sensors cleaned and filters changed. Master side system has a pan that almost completely rusted thru and customer was made aware she is one clog away from ceiling damage. No ther issues found at this time. Will leave quotes for pan replacement and drain line correction.
Form completed and attached. Recommended room sensors on the thermostats given their bad locations.
HVAC Service - Upon arrival checked in with customer the following are my findings Found the unit Working properly at this time this was the 1st maintenance of the system's life everything is checking out great electrically only recommendation is continual maintenance found 0 parts per million for carbon dioxide and no natural gas leaking at this time Inform the office about the Crown molding going back on the Access they will schedule somebody to come back out and remediate
1 system maintenance on trane gas unit. Form completed with recommendations. Can confirm heat is running st this time.
1 system checkup a trane gas unit. Form completed with recommendations. System has short cycle times and has low gas pressure resulting in only a 30 degree heat rise. System was left as is due to not wanting to shorten on off times any further. Customer was made aware.
Form completed with recommendations and pictures. Can confirm heat is tunning st this time.
Found flame sensor loose and wasnt in front of flame .I tightened flame sensor and tested in heat to verify it detected the sensor. No charge since we were out here friday .
1 system checkout on a trane gas unit. Form completed with recommendations and pictures. Can confirm heat is running at this time.
1 system checkup on trane 90% furnace. Form completed with pictures and recommendations attached. No issues found at this time.
Checked all gas line, flame sensor , igniter, inducer motor amps and inspected flu pipe . Checked blower motor wiring and amps . Changed filter and inspected ducts for air leaks or restrictions as well as condensate lines .brand new system .
Checked gas line , flame sensor , igniter, inducer motor amps and inspected flu pipe . Checked blower motor wiring and amps . Replaced filter and checked ducts for air leaks as well as condensate lines.
Checked both gas lines ,and performed co test , checked flame sensors , igniter,s inducer motor amps and inspected flu pipe . Checked blower motor wiring and amps . Checked filter and ducts as well as condensate lines.
2 system checkup on trane gas units. Form filled out and has all recommendations and issues listed on it. Can confirm heat is running at this time but with issues that should be addressed.
Form completed and quote will be attached. Can confirm heat is running at this time.