Jeff was quick and professional. He solved the issue!
Always attentive to details, no unnecessary sales pressure or “upgrades.” Professional and quality work that you can rely on.
Fransisco was fabulous!
Jeff was efficient and professional
Well mannered professional technicians.
Jason Deweese has an Excellent customer service! Very polite and explains everything before he do his work. He deserves a “Salary Increse”!!!
Efficient and Professional
System is out of refrigerant airhandler is leaking. Whole system needs to be replaced. Will set comfort advisor to give price on complete system.
Completed diagnosis, will need to come tomorrow and set blower ramp rate.
Completed maintenance check out, washed condenser coils, drains are clear, run capacitor, blower, fan motor and compressor amps are in range. Refrigerant levels are good, no problems at this time
Installed variable speed motor/module, checked operations working great
Completed check out, system is frozen. Blower motor module is faulty. We need to order part ASAP. Call and give price. M#TUHMD120ACV5VAA. S#10055PTU7G
Maintenance check is complete, condenser coils are clean, flushed primary drains, replaced media filter, checked run capacitor and start assist. Refrigerant levels and contactors are good.
Completed diagnosis, main breaker was in off position, checked out Compressor on start up and run capacitor. Everything checked out good.
Completed a/c maintenance check out. Run for compressor was out of range, installed Turbo capacitor. Also customer purchased gold membership. Inspected drain which was clear, compressor amps and fan motor is working properly. Refrigerant levels were good.
Installed 3/4 horse power 115 volt blower motor and 20 run capacitor. Everything is working fine. Also replaced blower wheel.
Completed diagnosis, found bad blower motor and run capacitor. Price to be paid 533.18. Reschedule for tomorrow.
AC performance tuneup times one system. Inspect blower, evaporator and ductwork. Changed out wireless thermostat to Trane 824 Wi-Fi. Check outdoor unit. Refrigerant level good at this time. Verified primary drain is clear. Washed condenser coil. System operating at manufacture specs at this time.
A/C maintenance check out is complete. Washed condenser coils, flushed drains, run capacitors and refrigerant levels were good. Blower, fan motor and compressor amps were in range. Recommended adding hard start assist.
Completed diagnostic on downstairs system. Performed electronic leak search, evaporator coil has multiple leaks in it. Price on horizontal carrier box coil. 3,400.00 on replacement M# CNPHP4821ATAABAA. S#3611X32809
System not keeping up. Arrived to find unit running but low on refrigerant. Added 3 pounds R 22 to achieve 12Â° sub cool. Universal condenser fan motor had a week run capacitor. Used dual capacitor to power fan. Washed condenser coil. System cooling properly at this time.
No cool single unit. Fan running all the time not shutting off. The client recently changed out thermostat thinking that was the issue. I found the original thermostat With incorrect wiring. Made adjustments to make it correct. Verified charge is good. System is operating at manufacture specs at this time.